Equipment spacing in the plant design and piping discipline is one area that continues to resist automation. Sure there are in-house and third party programs out there that assist designers in developing plot plans. Most of these programs are just overlays on CADD products. These 2D/3D CADD overlays may give feedback on costs of the arrangement – or – these 2D/3D CADD overlays may speed up the development of the plot by automating the generation of equipment graphics and structural graphics. However there are no tools out there that will arrange a plot plan automatically.
The main reason for this lack of equipment arrangement automation is the inability to develop rules that completely define how a list of equipment shall be arranged on a plot. The difficulty in defining equipment arrangement rules is due to the complexity involved.
Here is a partial list of the equipment arrangement design considerations that must be addressed on each project.
- High hazard operations
- Grouped operations
- Critical operations
- Number of personnel at risk
- Concentration of property and business interruption values
- Equipment replacement and installation time
- Interdependency of facilities
- Critical customer or supplier relationships
- Market share concerns
- Fire and explosion exposures
- Corrosive or incompatible materials exposures
- Vapor cloud explosions
- Sources of ignition
- Maintenance and emergency accessibility
- Drainage and grade sloping
- Prevailing wind conditions
- Natural hazards and climate
- Future expansions
- External exposures
The design consideration for ‘Vapor Cloud Explosions’ alone is a subject that fills books. The analytical automation tools for studying Boiling Liquid Evaporating Vapor Explosions (BLEVE) are few and are proprietary. There is documentation on how to evaluate BLEVE impacts using hand calculations, such as the TNT equivalency method. However it is generally accepted that these hand calculation methods do a poor job of predicting BLEVE.
And BLEVEs are just one form of Vapor Cloud explosions! Other types of vapor cloud explosions require different analytical techniques.
So what does the designer do? Designers the world over generally rely on their company’s (or their client’s) table standard that lists how far one piece of equipment needs to be from another piece of equipment. These tables are typically generated based on experience – particularly the experience of the insurance industry. A sample chart from the Bausbacher/Hunt book is shown above.
The following pages are going to compare and discuss the various spacing criteria available in the public domain. We will also try to point out where these criteria conflict, and where they may be weak.
By the way, the picture to the right is of a recent explosion in a plant where the spacing criteria satisfied an insurance group’s requirements for equipment spacing. The initial explosion caused a domino effect that leveled three units.
Table of Contents
1. Tankage Grouping
2. Classification of Crude Oil and Its Derivatives
3. Tankage Layout
4. Pump Areas
5. Fire Protection
6. Road and Rail Loading Facilities
1. Tankage Grouping
Tankage area will be subdivided into various groups determined by the contents of the tanks and the relative shape and area of the plot available, access and fire fighting must also be considered. See below table API tank size for layout purposes.
2. Classification of Crude Oil and Its Derivatives
Crude oil and its derivatives are potentially hazardous materials. The degree of the hazard is determined essentially by volatility and flash point.
The Institute of Petroleum has specified the following classes:
|Class 0||Liquified petroleum gases (LPG)|
|Class I||Liquids which have flash points below 21 oC|
|Class II||(1)||Liquids which have flash points from 21 oC upto and including 55 oC handled, below flash point|
|Class II||(2)||Liquids which have flash points from 21 oC upto and including 55 oC handled, at or above flash point|
|Class III||(1)||Liquids which have flash points above 55 oC upto and including 100 oC handled, below flash point|
|Class III||(2)||Liquids which have flash points above 55 oC upto and including 100 oC handled, above flash point|
|Unclassified.||Liquids with flash points above 100 oC|
For further information see IP refinery safety code part 3.
3. Tankage Layout
The layout of tanks, as distinct from their spacing, should always take into consideration the accessibility needed for fire-fighting and the potential value of a storage tank farm in providing a buffer area between process plant and public roads, houses, etc. , for environmental reasons.
The location of tankage relative to process units must be such as to ensure maximum safety from possible incidents.
Primarily requirements for the layout of refinery tanks farms are summarised as follows.
- Inter tank spacings and separation distances between tank and boundary line and tank and other facilities are of fundamental importance. (See 3.2) .
- Suitable roadways should be provided for approach to tank sites by mobile fire fighting equipment and personnel.
- The fire water system should be laid out to provide adequate fire protection to all parts of the storage area and the transfer facilities.
- Bunding and draining of the area surrounding the tanks should be such that a spillage from any tank can be controlled to minimise subsequent damage to the tank and its contents. They should also minimise the possibility of other tanks being involved.
- Tank farms should preferably not be located at higher levels than process units in the same catchment area.
- Storage tanks holding flammable liquids should be installed in such a way that any spill will not flow towards a process area or any other source of ignition.
3.2. Spacing of Tanks for LPG Stocks of Class 0
|Factor||Recommendations for LPG Stored in Pressure Tanks|
|1. Between LPG pressure storage tanks||One quarter of the sum of the diameters of the two adjacent tanks.|
|2. To Class I, II, or III product tanks.||15 M from the top of the surrounding Class I, II or III product tanks.|
|3. To low pressure refrigerated LPG tanks.||One diameter of the largest low pressure refrigerated storage tanks but not less than 30 M.|
|4. To building containing flammable material e.g. filling shed, storage building.||15 M|
|5. To boundary or any fixed source of ignition.||Related to water capacity of tank as follows :|
|Capacity Up to 135 cu.M Over 135 to 565 cu.M Over 565 cu.M||Distance 15 M 24 M 30 M|
The distance given in the above table are minimum recommendations for aboveground tanks and refer to the horizontal distance in plan between the nearest point on the storage tank and a specified feature, e.g. an adjacent storage tank, building, boundary. The distances are for both spherical and cylindrical tanks.
3.3 Bunding and Grouping of LPG Tanks
The provision of bunds around LPG pressure storage tanks is not normally justified.
Separation kerbs, low to avoid gas traps, maximum 600 mm high, may be located to prevent spillage reaching important areas, e.g. pump manifold area, pipe track.
Ground under tanks should be graded to levels which ensure that any spillage has a preferential flow away from the tank.
Pits and depressions, other than those which have been provided as catchment areas, should be avoided to prevent the forming of gas pockets.
Pressure storage tanks for LPG should not be located within the bunded enclosures of Class I, II or III product tankage or of low pressure refrigerated LPG tankage.
The layout and grouping of tanks, as distinct from spacing, should receive careful consideration with the view of accessibility for fire fighting and the avoidance of spillage from one tank flowing towards the other tank or towards a nearby important area.
3.4 Spacing of Tanks for Low Pressure Refrigerated LPG Storage Class 0
|Factor||Recommendations for Low Pressure Refrigerated LPG Storage|
|1. Between refrigerated LPG storage tanks||One half of the sum of the diameters of the two adjacent tanks.|
|2. To Class I, II, or III product tanks.||One diameter of the largest refrigerated storage tank but not less than 30 M.|
|3. To pressure storage tanks.||One diameter of the largest refrigerated storage tank but not less than 30 M.|
|4. To process units, office building, work-shop, laboratory, warehouse, boundary, or any fixed source of ignition.||45 M|
The distance given in the above table are minimum recommendations and refer to the horizontal distance in plan between the nearest point on the storage tank and a specified feature, e.g. an adjacent storage tank, building, boundary.
3.5. Bund or Impounded Basin for Refrigerated LPG Storage
A bund should be provided around all low pressure tanks containing refrigerated LPG. The tank should be completely surrounded by the bund, unless the topography of the area is such, either naturally or by construction, that spills can be directed quickly and safely, by gravity drainage and diversion walls if required, to a depression or impounding basin located within the boundary of the plant.
Bunds should be designed to be of sufficient strength to withstand the pressure to which they would be subjected if the volume within the bunded enclosure were filled with water. The area within the bund, depression, or impounding basis should be isolated from any outside drainage system by a valve, normally closed unless the area is being drained of water under controlled conditions.
Where only one tank is within the bund, the capacity of the bunded enclosure, including the capacity of any depression or impounding basis, should be 75 per cent of the tank capacity. Where more than one tank is within the main enclosure, intermediate bunds should be provided, so as to give an enclosure around each tank of 50 per cent of the capacity of that tank, and the minimum effective capacity of the main enclosure, including any depression or impounding basin, should be 100 per cent of the capacity of the largest tank, after allowing for the volume of the enclosure occupied by the remaining tanks. It is desirable for the required capacity to be provided with bunds not exceeding an average height of 6 foot as measured from the outside ground level.
The area within the bund should be graded to levels which ensure that any spillage has a preferential flow away from the tank.
No tankage other than low pressure tankage for refrigerated LPG should be within the bund. The layout and grouping of tanks, as distinct from spacing, should receive careful consideration with the view of accessibility for fire fighting.
3.6 Piping Installation and Flexibility
Liquid and vapour pipelines should have adequate flexibility to accommodate any settlement of tanks or other equipment, thermal expansion or other stresses that may occur in the pipe work system.
Precaution must be taken to prevent drain or sample valves freezing in the open position. The flow diagram will indicate the type of double valving to be installed, with a minimum distance between the valves of 1 meter. Do not allow liquid traps in vent lines.
3.7 Spacing of Tank for Petroleum Stocks of Classes I, II and III (2) .
|Factor||Type of Tank Roof||Recommended Minimum Distance|
|1. Within a group of small tanks||Fixed or Floating||Determined solely by construction / maintenance operational convenience|
|2. Between a group of small tanks or other larger tanks.||Fixed or Floating||10 M minimum, otherwise determined by the size of the larger tanks (see 3 below)|
|3. Between adjacent individual tanks (other than small tanks).||(a)Fixed||Half the diameter of the larger tank, but not than 10 M and need not be more than 15 M.|
|(b)Fixed||0.3 times the diameter of the larger tank, but not less than 10 M and need not be more than 15 M. (In the case of crude oil tankage this 15 M option does not apply)|
|4. Between a tank and the top of the inside of the wall of its compound||Fixed or Floating||Distance equal to not less than half the height of the tank. (Access around the tank at compound grade level must be maintained)|
|5. Between any tank in a group of tanks and the inside top of the adjacent compound wall.||Fixed or Floating|
|6. Between a tank and a public boundary fence.||Fixed or Floating||Not less than 30 M|
|7. Between the top of the inside of the wall of a tank compound and a public boundary fence or to any fixed ignition source.||
|Not less than 15 M|
|8. Between a tank and the battery limit of a process plant.||Fixed or Floating||Not less than 30 M|
|9. Between the top of the inside wall of a tank compound and the battery limit of a process plant||
|Not less than 15 M|
The table above gives a guidance on the minimum tank spacing for Class I, II and III (2) storage facilities, the following points should be noted.
- Tanks of diameter up to 10 M are classed as small tanks
- Small tanks may be sited together in groups, no group having an aggregate capacity of more than 8000 m3. Such a group may be regarded as one tank.
- Where future changes of service of a storage tank are anticipated the layout and spacing should be designed for the most stringent case.
- For reasons of fire fighting access there should be no more than two rows of tanks between adjacent access roads.
- Fixed roof with internal floating covers should be treated for spacing purposes as fixed roof tanks.
- Where fixed roof and floating roof tanks are adjacent, spacing should be on the basis of the tank(s) with the most stringent conditions.
- Where tanks are erected on compressible soils, the distance between adjacent tanks should be sufficient to avoid excessive distortion. This can be caused by additional settlements of the ground where the stressed soil zone of one tank overlaps that of the adjacent tank.
- For Class III (1) and unclassified petroleum stocks, spacing of tanks is governed only by constructional and operational convenience. However, the spacing of Class III (1) tankage from Class I, II or III (2) tankage is governed by the requirements for the latter.
- For typical tank installation, illustrating how the spacing guides are interpreted see below figures.
For details of a typical vertical tank foundation see below figures.
3.8 Tank Farm Piping and Layout
Pipelines connected to tanks should be designed so that stresses imposed are within the tank design limits. The settlement of the tank and the outward movement of the shell under the full hydrostatic pressure should be taken into account. The first pipe support from the tank should be located at a sufficient distance to prevent damage both to the line and to tank connections. Consideration may be given to installing spring supports near to tank connection for large bore pipework.
As large diameter tanks have a tendency to settle on their foundations, provision must be made in the suction and filling piping to take care of tank settlement. This may require the use of expansion joints, victaulic couplings, or a lap joint flange installed as shown in see below figure.
The following note must be added to all piping drawings containing storage tanks:
“All piping must be disconnected from tank during hydrostatic test of storage tank”
The number of pipelines in tank compounds should be kept to a minimum. They should be routed in the shortest practicable way to the main pipe tracks located outside the tank compounds, with adequate allowance for expansion.
Flexibility in piping systems may be provided through the use of bends, loops or offsets. Where space is a problem suitable expansion joints of the bellows type may be considered for installation in accordance with manufacturer’s design specifications and guides. These expansion joints should be used only in services where the fluid properties are such that plugging of the bellows cannot occur. They should be anchored and guided, should not be subjected to torsional loads, and should be capable of ready inspection.
Tank farm piping should preferably be run above ground on concrete or steel supports. Ground beneath piping should be so graded as to prevent the accumulation of surface water or product leakage. Manifolds should be located outside the tank bunds.
Piping should pass over earth bund walls, however, if this is impossible, a suitable pipe sleeve will be provided to allow for expansion and possible movement of the lines. The annular space should be properly sealed. Likewise lines passing through concrete bund walls will be provided with pipe sleeves.
Pedestrian walkways should be provided to give operational access over ground level pipelines.
Pipelines should be protected against uneven ground settlement where they pass under roadways, railways or other points subject to moving loads.
Buried pipelines should be protected externally by corrosion preventing materials, or by cathodic means.
Routes of buried pipelines should be adequately marked above ground and recorded.
Pipe racks carried across paths or roads should have adequate clearance from grade. Adequate access stairways or ladders and operating platforms should be provided to facilitate operation and maintenance at tanks. Tanks may be interconnected at roof level by bridge platforming.
All nozzles, including drains on a tank shell, should have block valves adjacent to the tank shell or as close as practicable.
3.9 Tank Bund Compound Capacities
Above ground tanks for Class I, II (1), II (2) and III (2) petroleum liquids should be completely surrounded by a wall or walls. Alternatively, it is acceptable to arrange that spillage or a major leak from any tank are directed quickly and safely by gravity to a depression or impounding basis at a convenient location.
The distance between the edge of the impounding basin and the nearest tank or the inside top of the nearest bund wall should be a minimum of 30 M. The distance between the edge of the basin and road fence battery limit of a process plant should not be less than 15 M.
The height of the bund wall as measured from outside ground level should be sufficient to afford protection for personnel when engaged in fire fighting and the wall should be located so that a reasonably close approach can be made to a tank fire to allow use of mobile fire fighting equipment. Access roads over bund walls into very large compounds are helpful in certain fire situations.
Separate walls around each tank are not necessary, but the total capacity of the tanks in one bunded area should be restricted to the following maximum figures:
|Single tanks||No restriction|
|Groups of floating roof tanks||120,000 m3|
|Groups of fixed roof tanks||60,000 m3|
|Crude tanks||Not more than two tanks of greater individual capacity than 60,000 m3|
The figures for b. and c. may be exceeded for groups of not more than three tanks, where there can be no risk of pollution or hazard to the public.
Intermediate walls of lesser height than the main bund walls may be provided to divide tankage into groups of a convenient size so as to contain small spillages and act as fire breaks.
Buried, semiburied or mounded tanks need not be enclosed by a bund wall except when they are located in ground higher than the surrounding terrain. However, consideration should be given to the provision of small bund walls around associated tank valves.
The net capacity of the tank compound should generally be equivalent to the capacity of the largest tank in the compound. However, a reduction of this capacity of 75% will provide reasonable protection against spillage and may be adopted where conditions are suitable (e.g. where there can be no risk of pollution or hazard to the public). The net capacity of a tank compound should be calculated by deducting from the total capacity a. the volume of all tanks, other than the largest, below the level of the top the compound wall and b. the volume of all intermediate walls.
A low wall which need not be more than 0.5 m high, should be constructed for Class III (1) and unclassified petroleum product tankage where conditions are such than any spillage or leakage could escape from the installation and cause damage to third party property drainage systems, rivers or waterways.
Where there is a possibility that tanks storing these products may be in the future required for Class I, II (1) or III (2), then the compound walls should be suitable for this potential situation.
4. Pump Areas
Pumps will be located outside bund areas. The vessels practice is to group the pumps into bays. Keep the suction lines as short as practical. The discharge piping will run on low level tracks to the process or loading areas. These tracks will usually pass under roads in culverts, but may pass over on a pipe bridge. Long pipe runs may require expansion loops to provide flexibility. Consult with stress section.
5. Fire Protection
For storage areas the major fire fighting effort will be provided by mobile equipment laying down large blankets of foam and/or applying large volumes of water for cooling purposes.
It is essential to provide a good system of all weather roads to facilitate the transfer of fire protection materials and equipment to the scene of the fire. These roads must be of adequate width and, wherever possible, with no deadends.
It is important in the siting of tanks, bund walls and access roads that the tanks can be protected by cooling water or foam appliances situated outside the compound walls. Account must be taken of the height of the tank and the possible need to cool the roof or project foam on to a tank.
Dry risers for foam may be provided to the top of storage tanks with their connections adjacent to access roads, fixed monitors may also be employed. The flow diagram will define the system to be employed.
6. Road and Rail Loading Facilities
Road and rail loading facilities are usually associated with storage area. The safe location of these in relation to storage tanks is laid down in section 3.7.
The road or railcar will be filled from a loading island, the supply lines will be either routed underground, or on an overhead pipe bridge. Check for clearances.
Below figures show such installations.
It has become common practice to provide a vapour collection system for the safe removal of vapours during the loading process. This system would employ unloading arms which are connected to a collection system and piped to a vent stack at a safe location.
When laying out a loading area consideration must be given to the number of vehicles or rail cars per hour to be loaded. A suitable movement pattern must be established for incoming and outgoing vehicles or railcars. Weigh bridges will be required, the system of moving rail cars must be defined, building housing, operation offices and facilities for drives etc. , must be provided.
API TANK SIZE – FOR LAYOUT PURPOSE
Based on API650
|US Barrels||CU Meters||Meters||Meters|
3; NO INTER-TANK SPACING REQUIREMENTS OTHER THAN FOR CONSTRUCTION / OPERATION / MAINTENANCE CONVENIENCE. TANKS D1 & D2 ARE TANKS WITH DIAMETERS GREATER THAN 10 m., & WITH DIAMETER OF D2 GREATER THAN D1.
Inter-tank spacings between small and larger tanks.
FLOATING ROOF TANKS OF DIAMETER D1 D2 D3 GREATER THAN 10 m. WITHIN THE SAME COMPUND. D1 GREATER THAN D2 & D2 GREATER THAN D3.
FIXED & FLOATING ROOF TANKS WITHIN THE SAME COMPOUND. D1 GREATER THAN D2, D2 EQUAL TO D3.
Inter-tank spacings for fixed and floating roof tanks (greater than 10 m diameter)
Lap joint Flange Detail for Tank Settlement
Foundation for vertical tank
Based on BS2654
Table of Contents
- Reboiler Connections
- Top Head Relief Valves
The fractionation column comprises a vertical cylinder interspaced at equal intervals with trays. Often these are in the form of simple perforated disks, but more complex arrangements occur depending upon column function. Contents are heated near the bottom producing vapours which rise up through the trays, meeting a flow of liquid passing down as a result of condensation occuring at various levels.
It is essential to ensure maximum surface contact between vapour and liquid. The lightest fractions are drawn from the highest elevations, the heaviest residue being deposited at the bottom.
It is necessary to establish whether column is working as a single unit or in conjunction with others similar. Dependent upon process arrangements flow may be sequential from one to the next. Thus for maximum economy order of columns must be arranged to give shortest piping runs and lowest pumping losses. Consideration should be given, where necessary, to material used, since although correct sequence may have been effected unnecessary expense may be involved with alloy lines. Such cases must be treated on their merits.
Column is interconnected with other process equipment so it must be located adjacent to pipe rack to allow piping connections to run to and from the rack in orderly fashion. Automatically this means that manways (provided for erection of trays and maintenance) should be located on the opposite side of the column away from the rack to provide suitable access for equipment required to be removed (see below figures). This is not mandatory since occasions arise when other arrangements are necessary.
Having located manways, orientate internal trays to ensure unimpeded access. Depending upon the type of tray used one or more downcomer partitions may be required. If these are orientated incorrectly entry will be impossible via manhole unless the column is exceptionally large. Preferably downcomers are arranged normal to manway access center line. Process connections can be located in logical sequence, starting from the top when tray orientation is established.
Highest connection is the overhead vapour line which is usually connected to a condensing unit. An air fin type unit may be located on top of the pipe rack. Alternatively a shell and tube exchanger type condenser is usually located on a structure adjacent to the column (as may air fin unit).
Overhead vapour connection may project vertically from top of the column followed by a 90° bend or it may emerge from the side at 45°, using an integral projection extending up almost to the center top inside the head (see below figure 9).
The latter is more economic in piping since it eliminates use of some expensive fittings especially when large diameter overhead lines are involved. It also makes piping supporting simpler as use of a 45° elbow enables pipe to run down close to the column. Disadvantage is greater rigidity making stress analysis more difficult.
Often permitted pressure drop between outlet nozzle and exchanger is low (i.e. approximately 0.5 PSI) thus it is essential to obtain straightest and shortest run possible. If connection is from the top special arrangements must be made for supporting the line which is often large diameter.
The condenser is usually self draining. Often some of the condensed liquid is required to be pumped back into the column (reflux). Thus the condensed liquid flows by gravity to a reflux drum situated immediately below the exchanger. This drum can also be mounted in the same structure supporting the exchanger. This is important since if it were located elsewhere an additional pump would be required if the liquid had to be elevated again after flowing from the condenser.
Furthermore, since the liquid in the reflux drum has to be returned to the column by a pump it is convenient to locate this underneath the reflux drum at the base of the structure.
It follows, therefore, that the orientation of the outlet of the vapour connection will automatically fix the location of the exchanger and the reflux drum or vice-versa. The reflux pump discharges back into the tower usually at a high elevation, and since the piping should be straight and as short as possible, it will probably come up at the side as the vapour connection.
Trays are numbered starting from the top. The first downcomer is therefore an odd one. Often the reflux connection is located above the top tray (see below figure 3). This means that orientation of the odd and even trays can be fixed since to utilize the tray contact surface, the reflux connection must occur on the opposite side of the downcomer.
The most important connections are the feeds (see figures 4 and 6). These may occur over the odd or even trays or a combination of both. Their elevational location is entirely a function of process design. Depending upon this, orientation of the nozzle will follow, but ensure that the nozzle is not located behind the downcomer from the tray above. This would result in a liquid build up in the downcomer restricting flow through the tray below and preventing correct operation.
Feed connections are usually located in the tray area between the downcomers in a manner to ensure maximum use of the tray area as possible. Often an internal feed pipe or sparger is used to facilitate this.
Instr ument connections must be arranged so that pressure connections are in the vapour space and temperature connections are immersed in the liquid.
Sometimes it is better to put the temperature connections in the downcomer part of the tray since the depth of liquid will be greater and it will be easier to obtain effective coverage.
Probe length and mechanical interference may prevent this, if so locate thermowell over the tray itself. This should be done only on installations where the liquid depth on the tray is sufficient (see below figure 8).
The base of the tower contains a level of liquid which is controlled by high and low level controllers, liquid level alarms and level gauges (see below figure 7). Care should be taken when orientating these instruments, that they do not obstruct access on the platform. Physical space that these instruments occupy can be excessive. Do not position immediately adjacent to ladders or manholes.
8. Reboiler Connections
Reboiler liquid and vapour connections are located either relevant to liquid head (elevation) or stress requirements, or both. Two configurations are possible :
For horizontal reboilers, consideration must be given to shortest most direct connection route to reduce pressure drop which will probably govern design layout. In both cases there may be support problems. Usually, a vertical reboiler (thermosyphon operated) offers the easiest solution.
Flexibility is obtained on the lower connection where entry into the bottom of the tower can be varied as required and support problems are simplified.
All of the above requires access of some kind. To minimise cost minimum platforming should be provided consistent with safety.
Orientation arrangements should be designed to avoid need for 360° platforms.
A platform should not extend almost entirely round the column simply to provide access to a temperature connection which could have been located on the oposite side. Where several columns may be working together, link platforms may be required to move from one to the next. In these cases strict consideration must be given to maximise economy.
Overall height is governed by a. number of trays, b. pump NPSH requirements and, c. static liquid head. This latter head necessary for thermosyphon reboiler establishes the skirt height.
Some circumstances require routing lines partially around the column. Should these lines cross a platform sufficient headroom clearance must be provided.
11. Top Head Relief Valves
Relief valves vary in number and size. Location can depend on whether discharge is to atmosphere or a closed system. If discharging to a closed system, locate at a convenient platform down the column above the relief header see below figure 5). If discharging to atmosphere locate on top of the column, with the open end of the discharge a minimum of 3000 mm above the top platform. For maintenance removal, valve should be located to allow top head davit to pick it up. Dependent upon size multiple relief valves may require a gantry structure on the top head.
Early orientation of nozzles and routing of lines allow platforms and pipe support clip locations to be passed to column vendor quickly.
It is becoming more a requirement that clips be welded on in the vessel fabrication shop particularly for alloy steels.
When locating platforms and ladders, the maximum ladder length should not exceed 9M without a rest platform.
Platforms should, where possible, be elevated 900 mm below manways.
Manways Davits or hinges should be positioned to avoid swing of cover fouling instruments or other connections.
When positioning vertical piping, to simplify supporting, attain a common back of pipe dimension from column shell of 300 mm.
Figures 1 – 8 Incl.
Table of Contents
- Reciprocating Compressors
- Centrifugal Compressors
Compressors are the mechanical means to increase vapor pressure, as pumps are used to increase liquid pressure .
There are two basic types of compressors, reciprocating and centrifugal. Each has one specific duty to intake vapor at low pressure, compress it and discharge it at a higher pressure. The quantity of vapor to be moved and discharge pressure it usually the deciding factor in the type selected .
1.1 Reciprocating compressors
Reciprocating compression is the force converted to pressure by the movement of the piston in a cylinder. These machine are generally specified for lower volumes than centrifugal compressors. If several stages of compression are employed, extremely high pressures may be developed. Because of their reciprocating action these machines cause piping, if not properly designed and supported, to pulsate, vibrate and generate fatigue .
1.2 Centrifugal Compressors
Centrifugal compression is the force converted to pressure when a gas is ejected by an impeller at increasing velocity. Centrifugal compressors are specified for large quantities of vapor. Pressure differential may be small or large. These machines are not subject to pulsation and therefore do not produce vibrational effects .
1.3 Compressor Drives
Drivers fall into three categories, i.e. electric, steam and gas.
Electrical drivers range from small flameproof motors to large motors, 2000 HP or more, requiring their own cooling systems . Steam drivers are comprised of single or multistage turbines, either fully condensing of backpressure . Gas drivers cover gas turbines or gas engines.
2. Reciprocating Compressors
2.1 Types of Machines
Reciprocating compressors can be obtained in a variety of patterns from a simple single cylinder to multicylinder multistage machines. See figure 1,2,3 for the most widely used patterns.
Figure 1 below is a single cylinder machine. It will operate at low speed, may be single or double acting.
Figure 2 is a balanced horizontally opposed multicylinder machine. It will operate at low speed, may be single or double acting, it can also be multistage .
Figure 3 is a gas fuelled angle – type engine. The compression cylinders are all on one side of the frame, cylinder diameters and lengths vary according to the composition, pressure and volume of gas to be compressed. Dimensions from frame center line to cylinder nozzles will vary with compression forces.
2.2 Types of Cylinders
Figure 3. Gas engine driven machine (note: gas engine may take ‘V’ form)
Figures 4,5 for details of cylinder arrangements.
Figure 4: single acting cylinder, having one suction, compression and discharge area per cylinder.
Figure 5 : double acting cylinder, having two suction, compression and discharge areas per cylinder.
Multicompression stages : number of times the vapor is compressed by going through a series of compression cylinders to increase pressure.
Gas compression raises temperature. In a reciprocating machine, compression is violent and heat rise is great. Inlet temperatures of 40 oC may be raised to over 100 oC by the act of compression. The cylinder gets hot and depending on the vapor being compressed, will need some form of cooling. This will usually be in the form of cooling water, but for low heat increases a glycol – filled jacket may suffice .
2.3 Compressor Foundation, Cylinder and Snubber Supports
The foundation for LP reciprocating compressors must be independent from all other foundations. It must support the compressor and all its auxiliary equipment.
Cylinder supports are supplied by the vendor if they are required.
They must be attached to the foundation concrete. Likewise the snubber supports must be attached to the foundation concrete, springs will be used locally to support the snubbers .
2.4 Compressor Layout
Effective compressor layout results in cost savings on process and utility piping, good maintenance accessibility and possibly reduced pulsation in suction and discharge piping. Poor layout does the opossite.
See below figure; TYPICAL LAYOUT OF COMPRESSOR HOUSE & SUCTION KNOCK OUT DRUM
For angle type compressors, locate the crankshaft parallel to the suction and discharge headers. For balanced horizontally opposed compressors, the crankshaft should run at right angles to the suction and discharge headers. Compressor houses containing more than one machine, particularly if they are long, will probably be equipped with a travelling gantry crane which will be manually or electrically operated. This feature can influence the overall dimensions of the house, as in addition to the necessary building and maintenance clearances, the vertical reactions of the loaded crane will increase foundation size. Since these must not be connected to the machine foundations, the building size will be affected. It is usual for compressor vendors to indicate the overall foundation dimensions on their layout drawings. (These should be requested as early as possible).
The compressor building must be sized very early in the layout stage when only preliminary dimensions are available. It may be known that the overall length of the machine is 6 meters and the width is 4 meters. To these dimensions must be added adequate clearance for maintenance plus possible control valve stations, lube oil equipment, local control panel, etc. Allow 2 meters all around the original dimensions. In practice this 2 meter allowance will provide a walkway of only 1200 – 1500 mm due to other items occupying floor space. With two or more machines, allow 2 meters between compression cylinders to allow for adequate piston removal. All dimensions must be confirmed from certified vendor drawings.
Allow a maintenance area at one end of the building. A 6 meter bay should be sufficient . Pits, trenches and similar gas traps should be avoided in gas compressor houses . Large reciprocating gas compressors will usually be elevated abovegrade with mezzanine floor level with the top of the foundation for operation and maintenance. The height of the mezzanine floor abovegrade will be kept to a minimum consistent with the adequacy of space for piping and access, especially to valves and drains .
2.5 Piping Layout
The piping layout will follow the plow diagrams as issued for the job. If they conflict with any of the following notes, the flow diagrams will always take precedence. It is usual for the suction piping to be routed to the top of the cylinder and discharge piping from the bottom. Liquids must be prevented from entering the compressors. As liquids do not compress, extensive precautions must be taken to ensure that absolutely no liquid enters the compressor cylinder ; a small quantity would do extensive damage.
If there is any doubt that the vapor is near its dew point, the suction line must be steam traced between the suction drum and the compressor inlet or local to the compressor inlet. Process Department will advise the extent and it will be shown on the flow diagram.
Suction and discharge headers will be located at grade level on sleepers up to the first piece of connecting equipment, e.g. suction KO drum or aftercooler. Branch connections to the compressor from the suction header will be taken from the top of the header . Suction and discharge piping will be kept as straight as possible between the compressors and headers. The use of short radius bends or tees and similar installations giving opposed flow shall not be permitted .
Piping shall not be less than compressor nozzle size. Piping local to cylinders shall clear the cylinder by sufficient distance to permit proper maintenance on the cylinder valves. When compressors are elevated with a mezzanine floor, piping and valves will normally run under the floor.
When more than one compressor is employed on the same service, all piping to and from the compressors will be valved so that any compressor may be shutdown and taken out of service. Spectacle blindes will be installed at the compressor side of the isolating valves.
Startup bypasses are to be installed between suction and discharge pipes of compressors and will be located between the compressor and the line block valve. When not furnished by the manufacturer, a relief valve will take be installed between the compressor discharge and block valve. This relief valve will discharge into the suction line downstream of the block valve. The relief valve will be provided with a bypass for hand venting.
Distance piece and packing vent piping will be manifolded into systems as indicated on the flow diagrams. These systems are either vented to atmosphere outside the compressor house or connected to a collection system.
Utility piping will comprise cooling water supply and return to lube oil cooler also to cylinder jackets. The minimum line size used will be 3/4” . Sufficient vents and drains will be provided so that water lines and jackets may be completely drained at shutdown. A steam or electrical supply may be required if lube oil heaters are provided for either the compressor or gear box oil. This system is used prior to startup.
Check for lines that have to be chemically and ensure drawings indicate this requirement .
3. Centrifugal Compressors
3.1 Types of Machine
Centrifugal compressors can be obtained in a variety of patterns. See figure 8. Centrifugal Radial Compressor
Centrifugal radial compressors ( figure 8) : the compression process is effected by rotating impellers of radial flow design ( figure 9 Radial Impellor) in fixed guide elements.
Centrifugal axial compressors ( figure 10) : the force is converted into pressure by rotating vanes between fixed guide vanes; the flow is axial .
3.2 Size and Position of Nozzles
Centrifugal compressor manufacturers have basic case designs; they change the rotor blade design to meet volume and pressure requirements. For this reason suction nozzles are sometimes much larger or smaller than the line size for hydrocarbon process applications. For example, a 30” suction nozzle may have a 20” or 24” suction line. It will be necessary to increase the suction line diameter locally at the compressor nozzle. Do not use a reducing flange as this will introduce full velocity to the rotor blades at a turbulent condition. Use 30” flange and a concentric reducer as a minimum. It is better if a pipe length of 3 dias of 30” pipe can also be accommodated .
Suction and discharge nozzles are either on the underside or the top of the compressor. On multistage compressors two or more inlet nozzles may be provided ; the suction lines are connected to suction drums controlled to maintain the various inlet pressures .
3.3 Compressor Foundations
(See fig.10 Centrigfugal axial compressors)
The foundation of each machine will be combined with its direct coupled drives but must be independent from all other foundations, including the lube console .
3.4 Compressor Layout
(See fig. 11,12,13 below)
Centrifugal compressors are usually large capacity machines. They are driven by electric motors, steam or gas turbine, the drive may be via a gearbox. It is usual to mount such machines on a tabletop about 4 meters high with elevated access all around. The lube and seal oil consoles for both the compressor and turbine, if used, will be located at grade. The suction and discharge connections of the compressor will most likely be on the underside; these lines can be anchored at grade. Should these connections be on the top of a horizontally split case compressor, see fig 13 for details of removable spools.
A typical compressor house layout is shown in figures 11 and 12. Here an electrical motor and a condensing type turbine has been used. Note the withdrawal and maintenance areas, also the acoustic hoods. Determine the type of travelling gantry crane, and ensure that piping, etc. is clear of it. Note the lube oil header tanks, these must be elevated above the machines, if the vendor has not stated a minimum elevation use 10 meters above the center line of the machines.
Their purpose is for emergency lubrication, and are tripped – in should the normal lubrication supply system fail. They supply oil to the bearings until the machine comes to a standstill .
The lube and seal oil consoles are comprised of the following items : oil storage tank, filters, pumps, oil cooler, sometimes an oil heater for startup, control instruments.
Interconnecting piping must be in accordance with the flow diagram, all return lines must be free – draining from the machines to the console.
Suction and discharge piping must be supported so that the nozzles are not overloaded, use reducers not reducing flange local to suction and discharge nozzles. Make provision for removal of strainers in the inlet line. Silencers may be required in both the suction and discharge piping.
Acoustic hoods may be required for both the compressor and turbine ; ensure that the tabletop is large enough to accommodate them. They may be of sectional construction. The travelling gantry crane will be used to dismantle them; this must be taken into consideration when determining the elevation of the crane hook.
Maintenance area must be large enough to accommodate the acoustic hood, turbine and compressor half casing rotors, etc.
4.1 Electrical Motors
Flameproof motors will be employed for small to medium HP machines.
Ensure that the cables can be routed to the terminations, also that there is space behind the motor to remove the rotor .
Large HP machines their own cooling systems ; these fall into two categories : CACW (close – air – circuit water cooled machine ) or CACA ( closed – air – circuit air cooled machine ) . These types of machines may require an area of 7 m x 7 m and, therefore, determine the size of the compressor house.
CACW machines (see fig. 14) : may be mounted on a tabletop with the cooler located under, in a sealed room. The cooling air circulating around the motor is itself cooled by water cooled heat exchanger. Provision must be made for removal and service of the exchanger.
It is possible to obtain motors with the cooler mounted above or to one side of the motor.
CACA machine consideration must be given regarding the safe location of the air intake, which will be outside the compressor house. If a filter is required in the intake system, provide access for replacement or cleaning .
4.2 Steam Turbines
Two types of steam turbines must be considered, condensing and noncondensing. The noncondensing type uses high pressure steam and exhausts lower pressure steam to a stream header. The condensing turbine exhausts to a surface condenser (which is usually a large exchanger with hot well attached, but may take the form of an air fan ) to recover condensate. Surface condensers are often grade-mounted directly below the compressors turbine. This arrangement employs a turbine with outlet nozzle directly connected via an expansion joint to the surface condenser. (See fig.16 ) . The surface condenser may be mounted at grade alongside a grade-mounted turbine. With arrangement very little NPSH is available.
If an air fan is used as a surface condenser it will usually be located above the turbine, either on the compressor house roof or over a pipe rack. If the condenser is the shell and tube type, it will most likely be of the fixed tube plate design and will require access for rodding the tubes. The cooling water lines associated with the condenser are large bore and some consideration must be given to the piping arrangement and placing of valves to give good operation and utilization of plot space.
The steam supply to the turbine will be taken from the top of the steam header, a bellow may be required local to the turbine and a temporary strainer will be used for startup.
The turbine will required a similar lube oil console to that provided for the compressor. Do not pocket the return drains. An elevated lube oil header tank also be required.
Noncondensing turbine assemblies comprise a turbine, lube oil console and header tank. The low pressure steam discharge line will be a large bore, a bellow will most likely be required in the line, which must join the top of the header. If the line has a low point, a steam trap and drip pocket must be provided.
Maintenance access : provision must be made to dismantle the acoustic hood, and remove half of the turbine casing and the rotor .
4.3 Gas Turbines
When using a gas turbine to drive a compressor, a similar arrangement to a steam turbine can be used; the lube oil console and header tanks will be required. In addition, the exhaust system must be considered; this will be comprised of ducting to some heat recovery system, either a steam raising plant or process heaters.
Combustion air to the turbine burner must be taken from a safe location outside the compressor house. Inlet silencer and filter will most likely be required. Provision for operation and maintenance to all machinery must be provided .
4.4 Gas Engines
Gas engines are used to drive reciprocating compressors, either directly or through a gearbox. The machine may have both compression and drive cylinder attached to a common crankshaft. These types of engines may develop 2,000 HP or more. Ensure that adequate space is allowed for removal of cylinder heads and pistons. The lube oil system may be integral with the engine that or in the form of a console. Should the latter be used, ensure that the engine is at suitable elevation to allow for free-draining oil return lines. (see fig.17)
The engine and compressor will be mounted on a common foundation that is independent of all other foundations. Due to the vibration produced by these machines, a large mass concrete foundation will be employed.
The general layout of the compressor house will enable the use of a travelling gantry crane for all maintenance, therefore when routing piping this must be considered. It is not likely that a mezzanine floor will be employed local to the machines, enabling most of the piping to be kept low.
Combustion air must be taken from a safe location outside the compressor house. If an air filter will be required, arrange for maintenance access. Likewise, the exhaust must be discharged outside the building.
This system will be fitted with a silencer and flame trap. Utility systems will comprise a start-up air system, also fuel gas. The engine will most likely have a closed circuit jacket water cooling system.
This will comprise a shell and tube exchanger or an air fan. If the former, cooling water supply will be required and the usual clearance for tube pulling, etc. will be provided. (see fig.18).
Figure 6: DETAIL OF FOUNDATION & SUPPORT FOR CYLINDER & SNUBBERS
Figure 7:TYPICAL LAYOUT OF COMPRESSOR HOUSE & SUCTION KNOCK OUT DRUM
FIG. 11 TYPICAL LAYOUT FOR COMPRESSORS ONE TURBINE DRIVEN ONE ELECTRIC MOTOR DRIVEN
Table of Contents
- Use of Exchangers
- Types of Exchangers
- Types of Shell and Tube Exchangers
- Layout of Shell and Tube Exchangers in Banks
- Alterations That Can Be Made to Shell and Tube Exchangers
- Establishing Elevations of Exchangers
- Layout of Exchangers Other Than in Banks
- Types of Air Fins
- Layout of Air Fins
- Fin Tube Exchangers
1. Use of Exchangers
Heat exchangers transfer heat from one media to another. In the petrochemical industry, they can be generally classified under the following headings :
Exchanger: Heats one stream and cools the other. There is no heat loss and physical change in either flowing media.
Cooler: Cools liquid or gases without condensation; applies also to intercooler and aftercooler.
Condenser: Condenses vapour or vapour mixture. Can be water – cooled or by sufficiently cold process stream which requires heating.
Chiller: Uses refrigerant for cooling process stream below freezing point or bellow prevailing cooling water temperature.
Heater (non fired) Heats process stream generally up to its boiling point without appreciable vaporization. Heating medium is usually steam; applies also to preheaters.
Reboiler: Reboils the bottom stream of tower for the fractionation process. Heating medium can be steam or hot process stream. When large quantities of vapor have to be produced the kettle type reboiler is used.
Waste heat boiler: Uses waste heat, such as internal combustion exhaust from gas turbines or similar drivers for steam generation.
Steam generator: Uses heat of process liquid or gas for producing steam.
Vapourizer: Vapourizes part of a process liquid stream as does an evaporator.
2. Types of Exchangers
Briefly, exchangers, etc. , can be divided into the following three groups :
Shell and tube: Which can be vertical or horizontal with the horizontal ones single or stacked in multi-units. As the name suggests, they consist of a cylindrical shell with a nest of tubes inside.
Fin tube:This consist of a finned tube through which passes one media jacketed by another tube through which passes the other media. They can be used as single or multi – units.
Air fins: Come in two shapes ; flat box units and “a” frame units. Both consist of banks of finned tubes through which passes the media to be cooled. Large fans blow air from atmosphere through the banks, thus cooling the flowing media. There are other types, such as plate exchangers, carbon block exchanger, etc., but these are used infrequently.
3. Types of Shell and Tube Exchangers
Floating head exchangers are used when the media being handled causes fairly rapid fouling, and the temperature creates expansion problems. Tubes can expand freely ; channel head and shell cover arrangement is convenient for inspection, and the tube bundle can easily be removed for cleaning.
U-tube exchangers are used when fouling of the tubes on the inside is unlikely. The tubes are free to expand and the bundle can be removed from the shell for cleaning on the shell side of tubes.
Fixed head exchangers have no provision for the tube expansion and unless a shell expansion joint is provided can only be used for relatively low temperature service.
The end covers are removable so that the inside of the tubes can be cleaned by rodding or other similar tools. This type of cleaning is usually carried out in situ so some space should be allowed in the piping layout to allow for this.
4. Layout of Shell and Tube Exchangers in Banks
For good maintenance and safe working conditions, it is necessary to space exchangers such that surrounding area is adequate and clear. They may be spaced apart and grouped in pairs. When apart, a clear access way of 750 mm is considered adequate, this being the clear space between the shells and/or the associated pipework and insulation. For paired exchangers a similar condition is required between pairs and adjacent singles, but between each shell of the pair this may be reduced to 450 mm between head flanges. Exchangers should always be arranged such that the ideally there is a minimum of 150 mm clear at the rear for removal of the bonnet and space provided for dropping it clear of the working area. At the front or channel end, a minimum distance of the tube length plus 2500 mm is considered good. This latter does not of course apply to exchangers located in structures were a total of 1500 mm would be sufficient.
Piping connected to heat exchangers is generally simple. Piping economy and good engineering design depend largely on knowing what alterations can be made to exchangers. In other words, the piping designer can influence the exchanger design. For example, the direction of flow, nozzle locations, etc. Alterations to exchangers of course, should not affect their duty and cost.
Money saved on simpler piping should not be spent on costly alterations to exchangers. The accompanying chart shows the possible alterations that may be instigated by the piping designers to typical shell and tube exchangers without affecting the thermal design. When contemplating such a change it should be remembered that generally the heated media should flow upward, and the cooled media flow downward. This is particularly important if there is a physical change taking place within the exchanger, such as vaporization or condensation. Typical example of this are:
Reboilers where the process stream enters the shell at the bottoms as a liquid and leaves at the top as a vapour after flowing through the tubes, and stream enters the shell near the top of the tubes and leaves at the bottom on the shell as condensate.
Condensers where the process stream enters the shell at the top as a vapour and leaves the bottom as a liquid, whilst cooling water enters the tubes side at the bottom and leaves at the top.
5. Alterations That Can Be Made to Shell and Tube Exchangers
Interchange, flowing media between the tube and shell side. This change is often possible, more so when the flowing media are similar, for example, liquid hydrocarbons. Preferably the hotter media should flow in the tube side to avoid heat losses through the shell, or the necessity for thicker insulation.
Change direction on flow on either tube or shell side. On most exchangers in petrochemical plants, these changes are frequently possible without affecting the required duty of the exchanger if the tubes are in double or multi – pass arrangement and the shell has cross flow arrangement.
In exchangers where counterflow conditions can be arranged, changing of flow direction should be made simultaneously in tube and shell. Some points to consider when contemplating a flow change are :
Shell leakage : When water cooling gases, liquid hydrocarbons or other streams of dangerous nature it is better to have the water in the shell and the process in the tubes, since any leakage of gas, etc. , will contaminate the water rather than leaking to atmosphere.
High pressure conditions : It is usually more economical to have high pressure in the tubes than in the shell as this allows for minimum wall thickness shell.
Corrosion : Corrosive fluids should pass through the tubes, thus allowing the use of carbon steel for the shell.
Fouling : It is preferable to pass the clean stream through the shell and the dirty through the tubes. This allows for easier cleaning. Mechanical changes, such as tangential or elbowed nozzles can sometimes assists in simplifying the piping or lowering stacked exchangers.
6. Establishing Elevations of Exchangers
Where process requirements dictate the elevation, it will usually be noted on the P and I diagram.
From the economic point of view, grade is the best location, where it is also more convenient for the tube bundle handling and general maintenance. Exchangers are located in structures when gravity flow is required to the collecting drum, or where the outlet is connected to a pump suction which has specific NPSH requirements. To elevate exchangers without specific requirements, the following procedure is recommended :
Select the exchanger with the largest bottom connection; add to the nozzle standout dimension ( center line of exchanger to face of flange ) the dimension thru hub of flange, elbow (1 1/2 dia ), one – half the O/S pipe diameter and 300 mm for clearance above grade.
Now subtract the center line to under-side of support dimension from above, and the dimension remaining is the finished height of the foundation including grout.
It is preferable if this foundation height can be made common for all the exchangers in the bank. If this is impracticable due to extremes of shell and/or connection pipe sizes, then perhaps two heights can be decided upon.
When stacking exchangers, two or three high, it is desirable that overall height does not exceed 12’ 0” (3650 mm ) due to the problem of maintenance, bundle pulling, etc.
Plan-wise the exchanger bank should be laid out spaced as noted previously, and all the channel nozzles on a common center line.
This is particularly important if the cooling water headers are underground, as the CW inlets can rise into the lower channel nozzles.
The end of the exchanger adjacent to the rack will normally be the fixed end, if the CW headers are underground the fixed end will become the channel end.
All changes proposed must be discussed fully with Process Engineer and Client Engineer or Vessel Department.
Lines turning right in the yard should be right from the exchanger center line and those turning left should approach the yard on the left-hand side of exchanger center line. Lines from bottom connections should also turn up on the right or the left side of exchangers depending upon which way the line turns in the yard. Lines with valves should turn towards the access aisle with valves and control valves arranged close to exchanger. Utility lines connecting to a header in the yard can be arranged on any side of exchanger center line without increasing pipe length.
Access to valve handwheels and instruments will influence piping arrangement around heat exchangers. Valve handwheels should be accessible from grade and from a convenient access way. These access ways should be utilized for arranging manifolds, control valves and instruments.
In the piping arrangement, provision for tube removal access should be provided. This means a spool piece of flanged elbow in the pipe line connecting to the channel nozzle.
The requirements of good piping layout generally apply to the design of heat exchanger piping. The shortest lines and least number of fittings – temperature permitting – will obviously provide the most economical piping arrangement. The designer should avoid loops, pockets and crossovers, and he should investigate, nozzle to nozzle, the whole length of piping routed from the exchanger to some other equipment, aiming to provide not more than one high point and one low point, no matter how long the line.
Very often a flat turn in the yard, an alternative position for control valves or manifold, changed nozzle location on the exchanger, etc. , can accomplish this requirement.
Avoid excessive piping strains on exchanger nozzles from actual weight of pipe and fittings and from forces of thermal expansion.
For valves and blindes the best location is directly at the exchanger nozzle. In the case of an elbow nozzle on an exchanger it should be checked that sufficient clearances are provided between valve handwheel and outside of exchanger. Elevated valves may require a chain operation. The chain should hang freely at accessible spot near the exchanger.
Below figure shows sketches highlighting exchanger piping details. Orifice flanges in exchanger piping are usually in horizontal pipe runs. These lines should be just above headroom, and the orifice itself accessible with mobile ladder. Orifices in a liquid line and mercury type measuring element require more height. At gas lines the U-tube can be above the line with orifice, consequently the height is not critical. Lines with orifice flanges should have the necessary straight runs before and after the orifice flanges required in specification or standards.
Locally mounted pressure – and temperature indicators on exchanger nozzles, on the shell or process lines, should be visible from the access aisles. Similarly gauge glasses and level controllers on exchangers should be visible and associated valves accessible from this aisles. When arranging instrument connections on exchangers sufficient clearances should be left between flanges and exchanger support between instruments and adjacent piping. Insulation of piping and exchangers should also be taken into account.
8. Layout of Exchangers Other Than in Banks
Process equipment in most plants is arranged in the sequence of process flow. However, whatever layout system is used, the general evaluation regarding exchanger positions is very similar.
In layout the fractionation towers should be located in proper sequence first, although often the arrangement of other equipment – for example, condensers depend directly upon the tower orientation, and sometimes the decision whether to use a structure or not depends upon this. This relative position of exchangers can be readily evaluated from flow diagrams. For exchanger positions in a petrochemical plant the following general classification can be made.
Exchangers which must be next to other equipment. Such exchangers are the reboilers which should be located to their respective towers, or condensers which should be next to their reflux drums close to the tower.
Exchangers which should be close to other process equipment. For example, exchangers in closed pump circuits such as some reflux circuits. Overhead condensers should also be close to their tower to ensure that the line pressure drop in minimal. In case of tower-bottom-draw-off-exchanger-pump flow, exchangers should be close to the tower or drum, to give short suction lines.
Exchangers located between distant items of process equipment. These are for example, exchangers with process lines connected to both shell and tube side. Where parallel run is the ideal location for this type of exchanger. On that side of the yard, where the majority of related equipment is placed. Other locations will cost more in pipe runs.
Exchangers located between process equipment and the unit limit. Such exchangers are for example product coolers. These are frequently located near the unit limit.
Stacked exchangers. A further step in the layout is to establish which exchangers can be stacked for simplifying piping and saving plot space. Most units in the same service are grouped automatically. Two exchangers in series or parallel are usually stacked. Sometimes, small diameter exchangers in series can be stacked three high. Two exchangers in dissimilar services can also be stacked. Sufficient clearance must be provided for shell and channel side piping between the two exchangers. Reboilers and single condensers usually stand by themselves beside their respective towers. Vertical thermosyphon reboilers are usually hung from the side of their associated tower.
9. Types of Air Fins
There are two types of air fin construction : the box type and the “A” frame type.
The box type can be divided into two forms : forced draught and induced draught.
Forced draft air fins are the most commonly used type, possibly because maintenance of the fan is easy from an underslung platform.
“A” frame type air fins less common than the box type.
They offer the advantage of requiring less plot area than box type air fins of the same capacity. They do, however, present a few problems. Due to physical shape of them, i.e. triangular section with the apex uppermost, the inlet header is located at the apex, with the collecting headers at both bottom corners. This means that cooled product lines are coming off both sides of the rack which can present piping problems. Also, with 60o sides containing the product, it is possible to get uneven cooling due to the sun being on one side, or the prevailing wind tending to blow into the tube bank against the fan.
10. Layout of Air Fins
Air fins are large compared with shell and tube exchangers, and it is not uncommon for them to occupy several thousand square feet of plot area on a unit.
If this plot area is required at grade, there could well be siting problems, but fortunately most process using air fins require a gravity feed through them, which means they must be elevated.
The most common satisfactory location is on top of the main pipe rack. Pipe rack width is invariably determined by tube length of air fin units. In the absence of sufficient room on the rack, they may be located on top of any suitable structure, or an elevated structure may be built for the purpose.
When locating air fins on the plot a number of points have to be borne in mind.
Air fin of a given capacity could be made up of several units each weighing several tons.
It is important that each unit be reached by the site crane for erection and maintenance purposes. Therefore, the overall plot layout must provide for this crane access.
As most air fins will be condensing overheads from towers, it is important to consider the explanation problems of the overhead line when siting the relevant air fin, as air fins are unsuitable for accepting high loads on the nozzles.
Access platforms are always provided either side of the air fin for access to the header boxes, and underneath the units for access to fans and motors. Provision must be made for grade to all these platforms at least at either end.
It is a good idea to investigate connecting these access ways to adjacent structures to provide intermediate escape and for operational convenience.
There are four major problems when piping-up airfins :
- Correct configurations of piping to give equal or as near equal distribution as possible of the product through each unit of multi-unit air fins.
- Make piping from tower overhead as short as possible to minimize pressure drop.
- Obtaining a piping system that is sufficiently flexible to avoid overloading the unit nozzles.
- Providing sufficiently suitable pipe supports and anchors.
Below figure shows diagrammatically three methods of piping for distribution :
- Showing good distribution
- Showing good distribution
- Showing bad distribution
When designing the piping for air fin exchangers, the basic rules of piping still apply, that the piping runs should be as short and direct as possible, but at the same time be sufficiently flexible to avoid overloading the air fin nozzles. The below figure shows two methods of running product headers to air fins :
By running the inlet header down the center of the units, the off-takes to the unit drop out of the bottom of the header, run across the units and drop into the nozzles.
Thus, we have a series of off-takes sufficiently long to absorb expansion, at the same time having the minimum of elbows resulting in minimum pressure drop.
Supports can usually be attached to the steel members that run between units and are thus short and minimal. The header must be flanged at intervals along its length to facilitate the removal of units by crane for maintenance.
The preferred position for the header is directly above the inlet nozzles, keeping the branches as short as possible. Make sure that the air fin is capable of excepting the movement imposed on the header. Support from the rack steel is between the header boxes.
Outlet headers are less of a problem because the temperature is lower and the pipe size usually much smaller.
They can usually be supported off the air fin legs beneath the header box platform.
Any valves required to isolate units are the best located on the unit nozzles. Sometimes air fins handling light hydrocarbons may require snuffing steam supply.
These should be treated in the same way as snuffing steam to heaters, insomuch as the valves should be located at least 15 meters radius planwise from the perimeter of the air fin.
Piping runs that place loads of any sort on the air fin structures should be avoided if possible, or communicated to the vendor as soon as possible.
12. Fin Tube Exchangers
Fin tube exchangers consist of a hairpin shaped inner tube with heat transfer fins on the outside, except for the return bend.
The two legs are jacketed with larger bore pipe.
The heat exchange is achieved by the stream passing through the hairpin, and the other passing through the jackets. They may be used singly or in multiples.
The primary uses are for heathers or coolers; that is, the process stream passes through the inner tube and either steam or cooling water passes through the jackets. They are used mainly as a source of local heat exchange, such as outlet heaters from the tanks and drums to pumps, etc.
Our important point to remember when locating fin tubes is that the hairpin tube draws out from the back end, that is, the opposite end from the nozzles, and sufficient room must be allowed for this purpose.
Piping design considerations are similar to those on shell and tube exchangers.
Chillers are used where the process stream requires cooling to lower temperature than possible with cooling water, and for this purpose it is necessary to use a refrigerant.
Depending upon the size of the chillers installation, the refrigerant can either be supplied by a proprietary package unit, or a custom-built job using LPG. The construction is similar to fin tube, insomuch as the tube within a tube feature is common.
Chillers usually consist of a multi-unit bank with the process stream passing through the inner tube and the refrigerant passing through the jackets. Once again space must be allowed at the rear for tube withdrawal. An important thing to remember when laying out these exchangers, is the considerable thickness of insulation required on all the pipe-work, necessitating larger than normal pipe spacing.
TYPICAL EXCHANGERS – SHOWS POSSIBLE ALTERATIONS FOR BETTER PIPING
AIRFIN MANIFOLD LAYOUT
HEADER MOUNTINGS FOR AIR FIN
Table of Contents
- Inlet and Outlet Piping
- Burner Piping
- Decoking and Sootblowing
The primary function of a fired heater is to supply all heat required by the process in one form or another. A fired heater utilizes gaseous or liquid fuels often produced as a by-product. The normal process function is raising the process stream to its required temperature for distillation, catalytic reaction, etc. Sizes of heater vary considerably, dependent upon the type of duty and throughput.
There are two general basic designs or types of fired heaters:
Either of which may be forced or natural draft.
BoxType Heaters (See below figures 2 and 3.)
A box type heater is considered to be any heater in which the tubes are horizontal. In this type of heater it is possible to have locations or zones of different heat densities. The zone of highest heat density is the “radiant section”. The tubes in this section are called “radiant tubes”.
The heat pickup in the radiant tubes is mainly by direct radiation from the heating flame. In some heater designs shield tubes are used between radiant and convection section. The zone of lower heat density is the “convection section”. The tubes in this section are called “convection tubes”. This heat pickup in the convection section is obtained from the combustion gases primarily by convection.
Box type heaters may be up-fired or down-fired with gas or oil fired burners located in the end or sidewalls, floor, roof or any combination thereof.
In the horizontal up-fired heater, products of combination in the radiation chamber pass upward through banks of roof tubes and a fire brick diffuser into a plenum or collecting chamber. From the plenum chamber flue gases are passed through an overhead convection section and then to an overhead stack. Such heaters may be fired vertically upward by panels, mounted in the heater floor or hearth, the heater floor being elevated to provide headroom beneath. Alternatively, these heaters may also be fired horizontally by burners mounted in the heater-end walls, in which case the heater floor is only elevated above grade to provide air cooling convection to the heater foundations. This type of heater may contain single or multiple radiation chambers discharging flue gases to a common convection section and stack.
In the down-fired heater, combustion gases generated in the radiant chamber pass downwards through a refractory checker hearth into a collecting chamber beneath. From there the flue gases flow upward through the convection section and then out to the stack. The down-fired heaters are basically intended to fire on heavy residual fuels, where the flue gases are corrosive and may clog flue gas passages of conventional heaters.
Convection sections are thus protected by removal of combustion solids and are usually provided with inspection ports, soot blowing devices and tube facilities to keep the coils clean. Burners in down-fired heaters are always mounted in the heater-end walls.
Vertical Heaters (See below figures 4,5 and 6) Vertical heaters are either cylindrical or rectangular. They may have radiant section only or convection and radiant sections. The radiant section tubes will usually be vertical, but some cylindrical heaters have helical coils. The convection section can be either vertical of horizontal.
Types of Heater Firing
Heaters can be fired from any position, i.e. bottom, top, side or end.
By far the most common is bottom fired, mainly because it is more economical. The burner of a bottom fired heater will be located 2.1-2.7 M above grade at a height which is suitable for an operator to work underneath. Operating from under the heater is more dangerous than other types of firing, which is the principle reason certain operating companies will not install a bottom fired heater.
Heaters are commonly light with an electric ignitor. some refineries use a propane torch while some still light the burners with a rag soaked in spirits or kerosene.
Forced or Natural Draft
Consideration must be given at the layout stage to accommodate the additional equipment associated with a forced draft heater. This will usually comprise an air inlet duct with silencer, forced draft fan and an air preheater. The inlet duct may require a support structure.
Heaters are always located at a safe distance 15 meters away from other hydrocarbon bearing equipment and preferably upwind; however, on some process it is permitted for reactors to be within this distance to prevent light volatile vapors from begin blown towards an open flame.
Space must be allowed for tube replacement for both horizontal and vertical heaters and this, together with ample access for mobile equipment, should be considered on piping layouts and drawings. Ample access is always needed for firefighting equipment with areas under or around heaters usually paved and curbed.
No low points in the paving or grading are permitted as these provide excellent sports for trapping hydrocarbon liquids which could be ignited by the open flames of the burners.
3.1 Snuffing Steam Station
See below figure 7.
Snuffing steam connections are supplied by the heater manufacturers, generally in the combustion chamber and header boxes.
The control point or snuffing steam manifold is generally located at least 15 meters away from the heater, is supplied by a live steam header and is ready for instantaneous use. Smothering lines should be free from low pockets and should be so arranged as to have all drains grouped near the manifold.
Collected condensate (apart from freezing and blocking lines) can, when blown into a hot furnace, result in serious damage. (Low points should be drilled 10 mm diameter or provided with spring opening auto-drain valves).
3.2 Monitor Nozzles
Some customers request that turret or monitor nozzles be located around the heater so that water for fighting a fire is instantly available. Controls for such nozzles should be located at least 15 meters away from the heater.
3.3 Utility Stations
Steam, air and service water connections should be provided near tube-ends of heaters. 3.4. Process Control StationsProcess feed and discharging block valves and flow control valves shall be located at a distance from the heater, if indicated as necessary by the engineering flow diagram or instructed by the Piping Specialist Engineer or Project Department.
3.5 Explosion Doors
Piping shall not obstruct explosion doors or tube-access doors.
4. Inlet and Outlet Piping
See below figures 8 and 9.
Flow distribution through a multipass heater is affected by the inlet and outlet manifolding. The piping arrangement at the inlet of the furnace is the more critical and requires careful attention.
4.1 Inlet Piping
Inlet piping should preferably be symmetrical and of the same length from the point where flow splits to the heater inlets. This refers to the number of bends, elbows and valves, as well as the number of straight runs of pipe and their location. piping should avoid dead-end tee branches and sharp turns. Unequal flow through any part of the heater would result in deposits of coke and overheating of tube walls.
4.2 Outlet Piping
On outlet piping, symmetry is not as critical as on the inlet; however, nonsymmetrical piping may contribute to possible coking and overheating of tubes. A nonreturn and a shutoff valve is usual at the outlet of the furnace to eliminate any reverse in the case of tube failure.
Because of the high temperature involved and length of pipe runs required to isolate the heaters, piping flexibility must be examined carefully. Some heater manufacturers will permit a limited amount of tube movement to take all or part of the piping expansion. This possibility should be investigated in conjunction with the Stress Department, by the Piping Design Office during the study stage. It is generally necessary to anchor the piping adjacent to the heater to remove stresses from the nozzles.
5. Burner Piping
See below figures 8 and 9.
Supply of fuel to individual burners is adjusted by individual valves. These should be so located that the burners can be operated while observing the flame through peepholes or burner openings.
All burner leads for gas and steam (atomizing) must be taken from the top of the headers, and fuel gas piping should be so arranged that there are no pockets in which condensate could collect. The fuel oil header must have full circulation; under no condition shall it be a dead-end line. Noncirculating branches to burners should be as short as possible or insulated together with atomizing steam.
A ring header around the furnace mounted a short distance above the peepholes, having vertical leads adjacent to the vertical doors to the burners, provides the greatest degree of visibility from the operator’s point of view.
Atomizing steam to be used in conjunction with fuel oil shall be taken the main steam supply header at or near the heater. Steam traps shall be provided to drain all low points in the atomizing steam system. Separate leads to each burner shall be taken from the top of the atomizing steam subheader. Shutoff valves shall be so located that they can be operated while observing the flames from the observations ports.
6. Decoking and Sootblowing
(See below figure 12)
The internal cleaning of tubes and fittings may be accomplished by several methods. One is to circulate gas oil through the coil after the heater has been shutdown but before the coils are steamed and waterwashed and prior to the opening and start of inspection work.
This method is effective if deposits in the coil are such that they will be softened or dissolved by gas oil. When tubes are coked or contain hard deposit, other methods may be used, such as steam air decoking and mechanical cleaning for coke deposits and chemical cleaning for salt deposits. Chemical cleaning and steam air decoking are preferable as they tend to clean the tube to bare metal. The chemical cleaning process requires circulation of an inhibited acid through the coil until all deposits have been softened and removed. This is usually followed by water washing to flush all deposits from the coil. Steam air decoking process consists of the use steam, the coil. Steam air decoking process consists of the use of steam, air and heat to remove the coke. The mechanics of decoking are:
a. Shrinking and cracking the coke loose by heating tubes from outside while steam blows coke from the coil.
b. Chemical reaction of hot coke with steam.
c. Chemical reaction of coke and oxygen in air.
Steam and air services are permanently connected to the heater. The heater outlet line incorporates a swing elbow which, during the decoking operation, is disconnected from the outlet line and connected to the decoking header. Care must be taken to allow sufficient access and platforming when the swing elbows are changed over. Coke is carried by this header to the drum or sump.
In some instances it may requested by the Process Department or Client that the decoking manifold is connected to allow for reverse flow during the decoking.
6.2 Soot Blowing
In some heaters the convection section contains tubes with extended surface in the form of either fins or studs. Extended surface tubes are used to increase the convection heat transfer area at low capital cost. Because of the tendency of extended surface tubes to foul when burning heavy oils, sootblowers are usually installed.
Sootblowers employ high pressure steam to clean the tube outer surfaces of soot and other foreign material. Sootblowers may be either automatic electric motor operated by a pushbutton at grade, or manual requiring operation from a platform located at the convection bank level. Care must be taken that sufficient clearance is allowed for the withdrawal of sootblowers.
Generally heaters are supplied with sootblowing facilities in the convection section although tubes may not be of the extended surface type.
a. Damper: Mechanical or pneumatically operated to control the draft through the stack.
b. Draft gauge (P and I)
c. Flue temperature (TI)
d. Orsat (O2 CO CO2 analyzer).
Instruments b., c. and d. are used to access the correct combustion conditions. Steam is supplied for the Orsat connection in the stack. Water is supplied to the O2 analyzer. Platforming for the access to the stack instruments is supplied with the heater.
7.2 Heater Body
a. Skin thermocouples or tube wall TI’s: to indicate overheating of tubes.
b. PI’s: to measure the draft pressure through the combustion section of the heater.
Figures 1-11 incl. Figure1. BOX TYPE HEATER PLAN
PROCESS PIPING BOX HEATHER
AFTER TUBES BECIME HEADED, STEAM IS INJECTED AT CONVECTION INLETS, VALVES “1”, “2”, “4” & “5” ARE CLOSED “3” IS OPEN.
TO START BURNING, STEAM FLOW IS REDUCED. AIR IS INTRODUCED BY OPENING VALVE “4”. FOR REVERSE FLOW, VALVES “2”, “3”, “4” & “6” ARE CLOSED, “1”& “5” ARE OPEN. VALVE “2” IS OPENED ONLY IF REVERSE BURNING IS REQUIRED. WHILE PASS “1” IS BEING DECOKED, STEAM IS INJECTED INTO PASS “2” TO KEEP TUBES COOL.
Table of Contents
- Centrifugal Pumps
- Reciprocating Pumps
- Rotary Pumps
- Pump Drivers
- Pump Harness Piping
In this context a pump is defined as a machine used to generate a pressure differential in order to propel liquid through a piping system from one location to another.
1.2 Types of Pump
The three basic types of pump are centrifugal, reciprocating, and rotary. See below figures.
Centrifugal pumps are the most common. They are more economic in service and require less maintenance than other types. Rotation of the impeller blades produces a reduction in pressure at the center of the impeller. This causes liquid to flow onto the impeller from the suction nozzle thrown outwards along the blades by centrifugal force leaving the blade tips via the pump volute finally leaving the discharge nozzle, in a smooth, nonpulsating flow.
Reciprocating pumps are used where a precise amount of liquid is required to be delivered, also where the delivery pressure required is higher than can be achieved with other types. The liquid is moved by means of a piston in a cylinder after being drawn into the cylinder, through an inlet valve, as the piston moves down the cylinder. As the piston moves back up the cylinder the liquid is discharged at a pre-set pressure controlled by delivery valve.
The liquid is ejected from the cylinder into the piping system in pulses which are transmitted to the suction and discharge piping, thus hold downs could be required on the piping system. Rotary pumps are used to move heavy or very viscous fluids. These employ mechanical means such as gear, cam and screw, to move the fluid.
2. Centrifugal Pumps
2.1 Nett Positive Suction Head
Centrifugal pumps must have their suction lines flooded at all times.
The suction piping has to be designed to avoid cavitation or prevent vopour entering the pump. Therefore, suction lines should fall continuously for a sufficient height from overhead source to pump.
The minimum vertical height required from source to pump suction is called the Nett Positive Suction Head, (NPSH). This is critical for efficient pump operation and must not be reduced. Vessel elevations are often dependent on the NPSH of its associated pump. See below figures.
2.2 Pump Types
There are three basic types of centrifugal pumps. Horizontal drive shaft with pump drive mounted remote from the line, vertical drive shaft with pump and drive mounted on the line, vertical barrel type with direct immersion suction facility. In each case the type refers to drive shaft direction.
The most common is the horizontal with its shaft in the horizontal, vertical in line pumps have their shafts vertical and the pump is installed in the pipe line, as a valve must be. Vertical can pumps are usually single stage, but horizontal and vertical can types can be multi-staged to obtain higher delivery pressures.
2.3 Suction Piping for Horizontal Pumps
Suction piping is usually one or two line sizes larger than the pump suction nozzle size. Suction piping more than two sizes larger should be queried with Process Department.
Suction Nozzle Orientation
Centrifugal pumps are supplied with suction nozzles on the end of pump casing, axially in line with impeller shaft, also on top or side of pump casing. Usually pumps are specified with end or top suction for general services. Side suction pumps, with side discharge are frequently selected for large water duty. Also side suction – side discharge pumps can be obtained in multi-stage form for higher pressure differentials. These pumps tend to become very long, so if plot space is tight, consideration should be given to purchasing the pump in vertical form with a sump at grade. See below figures.
Flexibility of Suction Lines
Consistent with good piping practice, pump suction lines should be as short as possible, but with enough flexibility to absorb any pipe movement caused by temperature differentials and to maintain pump nozzle loads to within those permitted by pump vendor. For further details refer to section on piping flexibility.
Suction Line Fittings
Due to suction line being larger than the suction nozzles, reducers are required in the line. Reducers should be as close as possible to nozzle. Eccentric reducers will be used with the flat on top for horizontal pumps. See below figures. For pumps with suction and discharge nozzles on top of casing, care must be taken to ensure that the flats on eccentric reducers are orientated so that suction and discharge lines do not foul each other. See below figures.
Temporary Startup Strainers
All pumps must have a temporary startup strainer in the suction line to prevent any pipe debris damaging the pump. Strainers will be located between pump suction block valve and pump. Strainers are available in the following styles : flat, basket, conical and bath or “tee” type.
For basket and conical types a removable spool piece must be provided downstream of suction block valve, which must not interfere with line supports. Both types have the advantage that the piping is left undisturbed and strainer element can be removed simply by removing the blind flange on the tee, thus leaving the piping and supports undisturbed. See below figures.
2.4 Discharge Piping for Horizontal Pumps
Generally, discharge piping is one or two sizes larger than the pump discharge nozzle size.
Discharge Line Fittings
Due to discharge line being larger than the discharge nozzle eccentric reducers are required in the line. Reducers should be as close as possible to the nozzle, with top suction – top discharge pumps, care must be taken to ensure that the flats on eccentric reducers are orientated so that the lines do not foul each other.
A pressure gauge is located in the discharge line, and should be upstream of the check and gate valves which are usually flanged together with a dripring between them. When a level switch for pump protection is installed in the discharge line, upstream of block valves, ensure good access for maintenance of switch.
To enable good access to valve handwheels and ease of supporting, the discharge line should be turned flat after reducer, and the line angled away from the nozzle to enable the line to be supported from grade. See below figures.
Avoid supporting large lines from piperack structures if possible, this enables minimum size beam sections to be used and better access for pump removal and maintenance.
2.5 Side Suction and Discharge Horizontal Pump
This type of pump is usually installed in a large duty service with large bore lines. Never connect an elbow flange fitting makeup to the nozzle of suction line coming down to the pump. Supply a straight piece of pipe two pipe diameters long between the nozzle and elbow.
The two diameter pipe length can be eliminated if the elbow is in the horizontal, only eliminate pipe length if available space is tight. See below figures
2.6 Vertical Pumps
Vertical pumps, also called can type or barrel type are used when available NPSH is very low or nonexistent.
Vertical In-Line Pumps
This type of pump is mounted directly into the pipe line, as a valve would be. For smaller sizes, the piping system supports the pump and motor, thus it is essential that the line is supported local to the pump to prevent the line moving when the pump is removed. Also ensure that there is good access to pump for maintenance and withdrawal with no overhead obstructions for lifting out pump. Larger size in-line pumps have feet or lugs on the casing for supporting from grade or steelwork.
Vertical Can or Barrel Type
Usually this type of pump is installed in cooling tower water circulating service, retention ponds, and applications where NPSH is low and suction is taken from a sump below grade. In most cases, there is no suction piping to be considered, but the discharge line must be routed to ensure good access for pump maintenance, with no overhead obstructions for pump removal by a crane. See below figures.
3. Reciprocating Pumps
3.1 Types of Pumps
There are three classes of reciprocating pumps, piston, plunger and diaphragm.
Piston pumps are generally used where medium to high delivery pressures are required, such a high pressure flushing of vessel interiors, etc. These can be obtained in multi-cylinder form and can be single or double acting. Plunger pumps are usually used for metering or proportioning.
Frequently a variable speed drive or stroke adjusting mechanism is provided to vary the flow as desired.
Diaphragm pumps are invariably air driven and very compact, also there are no seals or packing exposed to the liquid being pumped which makes them ideal for handling hazardous or toxic liquids. These are often used for sump pump out. See below figures.
4. Rotary Pumps
4.1 Types of Pumps
There are two main classes of rotary pumps, gear or screw.
Gear pumps are usually employed to pump oils and nonabrasive fluids.
Screw pumps are usually used to pump heavy viscous fluids and nonabrasive sludges. Apart from maintaining good access to pumps for operation and maintenance each case should be treated on an individual basis.
5. Pump Drivers
5.1 Types of Pump Drivers
The three most common types of driver are the electric motor, diesel engine, and steam turbine.
5.2 Electric motors are the most common pump driver and are of the totally enclosed, flame proof type suitable for zone 1 use. Their sizes range from small to very large which require their own cooling systems.
5.3 Diesel engines are usually to be found as drivers for fire-water pumps which are housed in a separate building away from the main complex.
5.4 Steam turbines used for pump drivers are ussualy single stage and the pump that they drive are invariably for standby service (spare).
5.4.1 Steam Nozzle Orientation
The steam inlet nozzle is usually on the right hand side when viewed from the pump coupling end of the turbine with the exhaust on the left hand side as standard. Turbines can be purchased with inlet and exhaust on the same side. This means that the piping designer can place the exhaust connection either on the same or opposite side from the inlet. Generally opposite side location of nozzles results in less piping congestion.
5.4.2 Inlet Piping
Steam inlets are furnished with strainers as part of the turbine for protection against pipe debris, therefore inlet piping must be designed with a removable section for strainer removal.
Steam supply to turbines must be moisture free at all times, otherwise damage to the turbine will occur if condensate enters the turbine while it is running. To separate condensate from steam a boot-leg must be installed up stream of the inlet block valve.
The two basic turbine installations are manual startup or automatic startup. The manual startup will have a gate valve in the steam supply near the turbine inlet. Upstream of the block valve a boot-leg must be installed with connections for blow-down and steam trap to remove any condensate in the steam supply. For automatic startup the gate valve is replaced with remote operated control valve, the boot-leg and traps are still required upstream as for manual startup.
Steam traps should be provided to keep the turbine casing free from condensate. These can be installed at the casing low point if a connection is provided or, on the outlet piping if the casing drains into the outlet system.
Note there must be a trap before any vertical rise which could form a pocket where condensate could collect.
5.4.3 Warm-up Bypass
On automatic startup a warm-up bypass must be provided around the control valve. This bypass is usually a “1” globe valve, and is partially opened to allow steam to keep the turbine constantly warm and slowly turning to prevent the shock of hot steam entering a cold turbine, and eliminate damage to turbine blades.
For manual startup it is recommended that a warm-up bypass be installed, but the job flowsheets will govern.
When a warm-up bypass is installed a steam trap on the casing keeps the system free of condensate. See below figures.
5.4.4 Exhaust Piping
Turbine exhausts are routed either to a closed exhaust steam system or to atmosphere. When exhaust is to a closed system there must be a block valve between turbine and main header, this block is always open during normal conditions and only closed for turbine maintenance or removal. Thought should be given to locating exhaust block valve on the piperack immediately before lines enter main header, this will prevent accidental closure of this valve. If the exhaust line is routed to atmosphere, the steam trap on turbine casing will not be installed, but replaced by gate valve partially open to allow condensate to drain off from casing. See below figures.
5.4.5 Rotor Withdrawal
Most small turbine casings are split along their horizontal axis and enough space above the turbine should be kept clear to allow for the top section of casing to be lifted clear of rotor by crane. See below figures.
6. Pump Harness Piping
Most pumps require external services to be piped to them for bearing cooling, bearing lubrication, seal flushing, venting and draining.
These requirements will be shown on utility flowsheets, and it is the piping designers responsibility to ensure that the actual geographic location of pumps with harnesses are correctly shown on the flowsheets. Though should be given to running subheaders to groups of pumps that have harness requirements. These subheaders must be sized and marked on flowsheet masters. Because branch lines to individual pumps are small diameter, i.e. 6 mm, it is advisable to take branch connections from the top of subheaders. This will eliminate pipe debris getting into the branch line and into the pump bearings, etc.
Care should be taken to ensure harness piping does not interfere with good operation and maintenance space.
The above diagrams indicate correct and incorrect methods of attaching suction piping.
Fig. 1 Shows air pocket formed along upper side of pipe by sing concentric reducer.
Fig. 2 (A) Horizontal ell directly into pump suction results in an unbalanced thrust on pump bearings. (B) Use spool piece 3 pipe diameters long or long radius ell with center vertical vane. (C) May be installed with or without spool piece but 2 pipe diameters spool is preferred.
Fig. 3 Shows proper method of connecting pump suction to a suction header in order to avoid air pockets.
Fig. 4 Represents a common error made suction piping to a centrifugal pump by placing piping over an embankment of a reservoir, or other obstruction.
SUCTION PIPING: The suction piping should be as direct and short as possible. In general it should be one or two sizes larger than pump nozzle. If changes from one pipe size to another are necessary, standard reducers should be used. Correct and incorrect ways are shown in the picture referred to above.
Table of Contents
- Pressure Relief Valve Installations
- Thermal Relief Valve Installations
- Rupture Disk Installation
- Venting Atmospheric and Low Pressure Storage Tanks
The design of a relief system is governed by the following:
– API.RP520 “design and installation of pressure – relieving systems in refineries”
– British Factory Acts, in relation to steam raising plants, if applicable
– Local authorities and Clients requirements
– Good engineering practice
The design of atmospheric and low pressure venting systems are governed by the following :
– API.RP2000 “Venting atmospheric and low pressure storage tanks”
– Local authorities and Clients requirements
– Good engineering practice
This guide is intended to cover methods of installation for pressure relief valves and their associated pipe work and fittings.
The installation of rupture disks.
Venting storage tanks.
3. Pressure Relief Valve Installations
For general requirements of relief valves installation at vessel or pipe work, see below figures.
Relief valves should be mounted in a vertical position only.
For optimum performance relief valves must be regularly serviced and maintained. To facilitate this, relief valves should be located to enable easy access and removal. Sufficient platform space must be provided around the valve. Provision of a lifting device should be considered for large relief valves.For typical installation of relief valves and piping, see below figures.
The system inlet and outlet piping shall be designed to provide for proper valve performance. To this end a complete relief system isometric showing the inlet and discharge piping of all relief valves included in the system will be produced. Below figures shows part of such a system, overall dimensions and line sizes should be included.
The system must first be approved by the Process Department for pressure drop, then by the Stress Section for stress. Should the piping be rerouted due to stress requirements Process Department must reapprove the system.
The inlet piping to a relief valve shall be designed so that the pressure drop does not exceed 3 percent of the relief valve set pressure, see below figures.
The most desirable installation is that in which the nominal size of the inlet branch piping is the same as or greater than, the nominal size of the valve inlet flange, and in which the length does not exceed the face to face dimensions of a standard tee and weld neck flange of the required pressure class. The configuration shown on the flow diagram must always be followed.
Relief valve systems designed to discharge against a constant pressure cannot tolerate a back pressure greater than 10% of the set pressure. Balanced bellows or Balanseal type relief valves which operate practically independent of the back pressure tolerate a much higher figure, but generally the higher the back pressure the lower the capacity of the relief valve. Due to this the discharge piping should be kept as direct as possible,see below figures.
The flow diagram will determine if the discharge is to atmosphere, or to a closed discharge header, see below figures for details.
It is poor practice to mount the relief valve at the end of a long, horizontal inlet pipe through which there is normally no flow
Foreign matter may accumulate or liquid may be trapped and may interfere with the operation of the valve or be the cause of more frequent valve maintenance.
Process laterals generally should not be connected to relief valve inlet piping, see below figure 4.
Proximity of other valves and equipment, the recommendations laid down in below figures 4, 6 and 7 should be followed if possible for the minimum number of straight pipe diameters between the device causing turbulence and the relief valve. The above does not apply to relief valves fitted with stop valves, see below figures.
Relief valves discharging into a relief header must be located at an elevation above the relief header so that the discharge line is free draining. Under no circumstances may the discharge line or the relief header be pocketed.
4. Thermal Relief Valve Installations
Thermal relief valves are provided on cooling services where a system can be locked in by isolating valves. The discharge from the relief valve should be piped to grade in offsite areas, to the nearest drain in process areas, follow details as shown on the flow diagram. See below figures for further details.
5. Rupture Disk Installation
A rupture disk device is a nonreclosing pressure relief device actuated by inlet static pressure and designed to function by the bursting of a pressure containing disk. The disk may be made of metal or carbon graphite and housed in a suitable holder.
The purpose of installing a rupture disk up stream of a relief valve is to minimise the loss by leakage through the valve of valuable, noxious or otherwise hazardous materials or to prevent corrosive gases from reaching the relief valve internals, see below figure 11. Typical bursting disk installation at a relief valve.
The installation of a rupture disk may be called for down stream of a relief valve. In this case its purpose is to prevent corrosive gases from a common discharge line reaching the relief valve internals.
Rupture disks may also be installed as a sole relief device, see below figure 10.
Rupture disks must always be installed as shown on the vendors drawing. For example of a Concave installation see figure 10 and a Convex installation see figure 11.
6. Venting Atmospheric and Low Pressure Storage Tanks
Determination of venting requirements
Inbreathing results from maximum outflow of oil from tank, or from contraction of vapors caused by maximum decrease in atmospheric temperature. A vacuum breaking device is fitted directly to the line or vessel to prevent its collapse when the internal pressure falls below atmospheric. If the admission of oxygen into the process is hazardous, a inert gas supply is connected to the vacuum breaker via a pressure reducing valve. Follow the system defined on the Flow Diagram.
Outbreathing results from maximum inflow of oil into tanks and maximum which result from maximum increase in atmospheric temperature (thermal breathing). One of the following devices may be specified on the flow diagram.
Relief valve may be used either discharging to atmosphere or into a closed system.
Open vent with flame arresting device. Manhole or gauge hatch that permits the cover to lift.
Pressure and vacuum breathing valves are designed to prevent evaporation from storage tanks, but to allow breathing when the pressure or vacuum exceeds that specified. For details see below figures..
Figures 1 – 8 Incl.
RECOMMENDED TYPICAL RELIEF VALVE INSTALLATION (BASED ON API RP 520)
RECOMMENDED TYPICAL RELIEF VALVE INSTALLATIONS (EXTRACTED FROM API RP 520)
RECOMMENDED TYPICAL RELIEF VALVE INSTALLATION
RECOMMENDED TYPICAL RELIEF VALVE INSTALLATION
RECOMMENDED TYPICAL RUPTURE DISK INSTALLATION
TYPICAL PRESSURE & VACUUM BREATHING VALVE
Table of Contents
- Information Required
- Evaluation of Information
- Line Identification
- Piperack Width
- Piperack Elevation
- Line Location in Piperacks
- Piping Economy in Piperack and its Influence on Plant Layout
- Piperack General Arrangement Checklist
- Trenched Piping (Civil Department)
- Underground Piping (by Civil Department)
The pipeway conveys all main process lines connecting distant pieces of equipment, relief and blowdown headers, all lines leaving and entering the plant, utility lines supplying steam, air, cooling water and inert gas to the plant. Electrical and instrument cable trays are usually routed in the pipeway. Pipeways are classified by their relative elevation to grade.
Overhead piping supported on steel or concrete bents.
Above ground piping supported on concrete sleepers at grade level. (Off site areas where equipment is well spaced out)
1.3 Trenched Piping ( by Civil Department )
Below ground piping laid in connection trenches. Costly and usually undesirable; unless trenches are wide, shallow and well vented, heavy gases may settle and crea
te a fire hazard through the length of the trench. For these reasons, only pump out lines, chemical sewers or chemical drain collection systems are sometimes placed in trenches and routed to a pit or underground collection tank.
1.4 Underground Piping ( by Civil Department )
Piping direct buried below ground level. Due to costly maintenance and the usually corrosive nature of soil, this method of routing is generally reserved for sewer and drain lines. In some plants, especially in cold climates, cooling water lines are buried below the frostline. This should be determined at the beginning of a job, is generally a Client request.
2. Information Required
2.1 Job Specification
Job specification SP….C100 contains design criteria, agreed between Company and Client, affecting piperack design:
- Battery limit, valving and spade requirements.
- Catwalk, platform and ladder access to valves and relief valves in piperack.
- Minimum headroom and clearances under overhead piping or supporting steel within areas
- Pipeways and secondary access ways
- Main access roads
- Rail roads
- Standard to be used for minimum spacing of lines in paperacks
- Handling and headroom requirements for equipment positioned under piperacks
- Operating and safety requirements affecting piperack and structure design
- Location of cooling water lines underground or above ground
- Trenched piping, if any.
2.2 Process Flow Diagrams
Process flow diagrams show main process lines and lines interconnecting process equipment.
2.3 Engineering Flow Diagrams
Engineering flow diagrams are developed from process flow diagrams and show:
- Pipe sizes. Pipe classes, and line number.
- All instrumentation.
- Equipment and lines requiring services, i.e. water steam, air, nitrogen etc.
2.4 Utility Flow Diagrams
Utility flow diagrams show the required services:
And any additional services peculiar to the plant being worked on, e.g.:
- And refrigeration lines, etc.
3. Evaluation of Information
3.1 Initial Evaluation
Use plot plan and process flow diagrams to make a preliminary assessment of which portion of process lines will be located in piperack and which lines will interconnect directly to nozzles on adjacent items of equipment. Draw lines to be located on piperacks on print of plot plan. Some idea of utility piping required must be established and included coordinate with Instrument and Electrical Section to assess what additional rack space may be required to accommodate cable trays. This action provides a preliminary visual idea of the piperack space required.
With the receipt of engineering flow diagrams and utility flow diagrams, a more complete and accurate assessment of rack space is possible. Utility headers generally run the whole length of the piperack, so should be taken into account when estimating additional space required. To assist Process Department in sizing utility headers in the pipeway a line routing on a repro of the plot plan, showing order of take-offs is required.
4. Line Identification
Certain types of piping require special consideration:
4.1 Process Lines
Lines interconnecting nozzles on process equipment more than 6M apart (closer speced equipment may be directly interconnecting inside piping areas).
- Products lines which run from vessels, exchangers or pump to battery / unit limits
- Crude or other charge lines entering the unit which run along piperack before connecting to process equipment, furnaces, exchangers, holding drums or booster pumps.
4.2 Relief Headers
Individual relief lines, blowdown lines and flare lines should be self draining from all relief valve outlets to knock-out drum, flare stack or to a point at the plant limit. To achieve this, lines will connect into the top of the header and at 45 degrees in direction of flow. To eliminate pockets, and obtain required slope to knock-out drum some relief headers must be placed above the main piperack.
4.3 Instrument and Electrical Cable Trays
Often instrument and electrical cable trays are supported on the piperack track. Space must be allocated to accommodate them from the outset. Due to the possibility of induced current interference instrument and communication cable trays must be located away from electrical and power cable trays. Consult with Instrument /Electrical Department for separation requirements.
5. Piperack Width
The width of piperack is influenced by :
- The number of lines
- Electrical/instrument cable trays.
- Space for future lines.
The width of a piperack may be calculated using the following method : First estimate number of lines as described. Add up the number of lines up to 18” diameter in the most dense section of the piperack.
The total width in meters (W) will be :
W = ( f x N x S ) + A meters
Where f, safety factor = 1.5, if the lines have been laid out as described in initial evaluation.
Where f, safety factor = 1.2, if the lines have been laid out as described under development.
N = number of lines below 18” diameter
S = average estimated spacing between lines in millimeters.
Usually – S = 300 mm
Usually – S = 230 mm ( if lines in piperack are smaller than 10” )
A = additional width required meters for :
- Lines larger than 18”.
- Future lines.
- Instrument and electrical cable trays.
- Any slot for pump discharge lines 500 mm – 1 meter.
The total width is thus obtained. If W is bigger than 9M usually two piperack levels will be required.
Note : At the beginning of a job, `W` should usually include 30 – 40% of clear space for future lines.
The width of the piperack may be increased or determined by the space requirement, and/or access to equipment arranged under the piperack.
Below figure shows typical piperacks bents with tabulated dimensions. Total available piperack width of each type of support is included. This table can be used for selection. The most commonly used piperack supports are types 2, 3, 4 and 5.
5.1 Spacing between Piperack Bents
Normal spacing between piperack bents varies between 4.6M to 6M.
This may be increased to a maximum of 8M consideration must be given to :
- Smaller lines which must be supported more frequently ( see Company design specification “recommended span between pipe supports” )
- Liquid filled lines requiring shorter span than gas filled lines
- Hot lines which span shorter distances than cold lines of the same size and wall thickness
- Insulated lines; small bore, cold – insulated lines due to weight of insulation must be supported at relatively short intervals
- Space requirements of equipment at grade can sometimes influence piperack bent spacing.
6. Piperack Elevation
Piperack elevation is determined by the highest requirement of the following :
- Headroom over main road
- Headroom for access to equipment under the piperack
- Headroom under lines interconnecting the piperack and equipment located outside.
The size of steel or concrete beam supporting overhead piping must be taken into consideration. Headroom requirements for each job are detailed in Company specification no. C100 and coordination procedure.
6.1 Elevation at Piperack Intersection
Where two two-tier piperacks meet, it is essential that elevations of lateral piperacks slot between elevations of main piperack.
Figure 2A illustrates this requirement. Choice of top elevation of lateral piperack midway between the top an bottom main piperack elevation allows turning up or down at the intersection.
Generally, lines running at right angles to main piperack are assigned elevations 500 mm to 1 meter higher or lower (depending on headroom requirements) than lines running in main piperack. 500 mm differential between pipe runs is the absolute minimum.
Figure 2B shows a piperack intersection where the respective main and lateral piperack elevations do not slot between each other. This design complicates routing of lines from piperack to the other, especially where lines run on the bottom levels of both piperacks. Avoid this design at all cost.
Where a single tier piperack turns through 90°, and all lines can be kept in the same sequence in both directions, no elevation difference is necessary. When lines sequence changes, introduce an elevation change at the turn. See below figures.
7. Line Location in Piperacks
7.1 One Tier Piperacks
Below figure shows a cross section of a single level piperack. Heavy lines (very large diameter lines, large bore lines full of liquid) regardless of service are placed over or near the piperack columns. This simplifies steelwork or concrete piperack design. Centrally loaded column and reduced bending moment on the beam will result in a lighter overall design.
Place process and relief lines next to these. Lines serving left hand areas of plant on left, lines serving right hand areas on the right.
The central piperack portion is reserved for utility lines which may serve both right and left hand areas on the plant. However, utility lines serving one or two pieces of equipment should be on the same side of the piperack as the equipment to which they connect.
Process lines which interconnect equipment on both sides of the piperack should be placed close to utility lines, and can be on either side of piperack, depending upon location of equipment they serve. The position of product lines is influenced by their routing after leaving the unit, right, (left) turning lines should be on the right (left) hand side of the piperack.
If possible, a centrally placed section of the piperack is reserved for future lines. This section should run the whole length of the piperack. Should this be impracticable, a series of smaller sections, running the whole length of the piperack, are to be provided. (see below figure).
7.2 Two Tier Piperacks
Where the number of lines dictate the use of a two level piperack, utility lines are placed on the top level and process lines on the bottom level. This is not a rigid rule and where piping economy dictates certain process lines may be routed on the top level. Line sequence arrangement should follow the philosophy outlined previously.
7.3 Position of Hot Lines
It is advantageous for pipe supports to group hot lines requiring expansion loops together, preferably on side of the piperack. Horizontally elevated loops over the piperack are commonly used to minimize the effects of expansion on hot lines, the hottest and largest line being on the outside. See below figures.
7.4 Line Spacing
For line spacing use “recommended piperack spacing” per table in Job Specification C100. It should be noted that in certain cases, it is necessary to deviate from the standards quoted above, e.g., see below figures at point “A” due to possible differential expansion line spacing may have to be increased to allow for movement of lines at start up.
To determine expansion of hot lines, use Company engineering guide, Attachment “thermal expansion of pipe materials”.
8. Piping Economy in Piperack and its Influence on Plant Layout
8.1 Piperack Layout
Plant layout determines the main piperack piping runs. The shape of piperack is the result of plant arrangements, site conditions, Client’s requirements and overall plant economy. See below figures.
Piping economy depends primarily on the length of lines routed in the piperack. Below figures shows critical dimensions which influence overall cost. These dimensions depend on overall plant layout and should be carefully considered when the plot is arranged.
Dimension “A”, (see below figures) is the total length of piperack and is governed by the number and size of equipment, structures and buildings arranged along both sides of the piperack. On average, 3 meters of piperack length are required per item of process equipment, good lay-out can reduce piperack length. (Thereby costs).
Equipment in pairs, stacked exchangers supported from towers, two vessels combined into one, closely located towers with common platforms, process equipment located – under piperack – are examples which help shorten piperack length. In a well arranged plant, average length of piperack per item of process equipment can be reduced to 2.1 meters to 2.4 meters.
Careful selection of dimensions B and C, below figure will minimize interconnection equipment on opposite sides of piperack. C is normally no more than 1.8 meters to 3 meters.
Dimensions D and E, (see below figure), minimize. Overgenerous dimensioning here will increase vertical pipe lengths. Maximize use of available platforms for access to valves. Where air fins are located above the piperack, use associated air fin maintenance platforms, modifying their extent if necessary. This method will be cheaper than adding special platforms in the piperack.
9. Piperack General Arrangement Checklist
Critically review piperack layout against latest information. Some lines should require rerouting for maximum piping economy. Check loops required for nesting. As many loops as possible should be combined in a loop bay having due regard to stress requirements.
9.1 Vibrating Lines
- Avoid changes in direction
- Avoid long overhanging bends without support
- Use bends where possible (check with job specification)
- Tees to be avoided as far as possible, flow should enter along run of tee and never in the branch.
Low point pockets to be avoided in the following lines :
- Steam (trap any pockets and dead ends)
- Blowdown (these lines must be self-draining)
- Caustic, acid and Phenol (all these services to be self draining)
- R.V.’s both inlet and outlet
- Vapour to knock-out pots
- Heavy products, bitumen, wax
- Pump suctions
- Lethal and toxic substances
High point pockets to be avoided in the following lines :
- Pump suctions
- Light ends
- Vapour/liquid mixes (hot tower bottoms – reflux lines)
- Crude lines
On hot lines, check shoe requirements and clearances at changes of direction (pipe expansion).
Provide vents at high points.
Provide drains at low points.
Provide steam traps at : low points, up-stream of loops and dead ends, via condensate drip legs.
On steam, air and condensate headers, take-offs to be from top of headers. RV headers high or low elevation. Before finalizing elevation of RV header consider elevation of all RV discharges and elevation of knock-out drum at flare.
Bends, if used : (check with job specification).
- Where lines change elevation bends may be used providing difference in elevation is adequate and specification permits
- Header take-offs in piperacks, use elbows
- Special piping:
- Catalyst lines 5D (minimum).
- Vibrating piping 5D.
- Small bore usually below 2” (Client preferred).
Pipe setting: to be avoided in large bore lines. Small bore lines to be set only where absolutely necessary.
Pipe Stress Department will advise which piping systems require formal stress analysis.
Supports : avoid long unsupported overhangs.
Steelwork clearances : check steelwork clearances for addition of fireproofing (lower elevation of piperack), brackets, gussets and thermal expansion of lines.
Concrete support clearances: check for local thickening of concrete columns due to method of fabrication adopted (i.e. corbels).
Valves: check clearances and accessibility. Make full of extending platforms for operation (i.e. air fin maintenance platforms).
Chain wheels: preferably do not use. However, if necessary, check chain clearances. Spading and valving at battery limit : check for accessibility if necessary, provide access platform.
This type of pipeway is generally associated with offsite areas where equipment is well spaced out, and land space is not a premium.
10.1 Pipetrack Width
Pipetrack width may be estimated using the method detailed previously for piperack.
10.2 Spacing of Pipetrack Sleepers
Pipetrack sleepers are relatively cheap thus piping economy is dictated by the recommended span of the smallest line in the track.
Where small bore lines are few, sleeper spacing may be determined by the pipe span of large bore lines provided small bore lines are supported off the larger lines at adequate intervals. An angle with “U” bolts is sufficient (check with Pipe Support Section).
For recommended pipe support spans, use Company standard.
On an average minimum span = 3 meters
maximum span = 6 meters
depending on line size and substance carried in pipes, (i.e. gas or liquid).
All lines must be supported. At changes of direction due to long overhangs, for narrow pipetracks a diagonal corner sleeper is recommended. On wide pipetracks, use alternative method of two short sleepers located near corner. See below figures.
10.3 Pipetrack Elevation
Pipetrack elevation is set by maintenance access to piping items located underneath the pipetrack, i.e. drains and steam traps. A minimum of 12”/300 mm clearance between underneath of lines and grade is recommended; where necessary, this may be increased to 18”/450 mm.
As pipetracks are generally single tier, no change in elevation is necessary at changes of direction. This is effected by use of a flat turn. See below figures.
For individual line elevation above sleeper, use Company job specification no. C4 “elevation of hot insulated lines”.
10.4 Line Location
Line location with reference to bore and weight is unnecessary, as all pipes are supported on sleepers which rest directly on the ground. Line routing is all important. All lines interconnecting process equipment and/or storage tanks located on left-hand side of pipetrack are placed to the left-hand side. Similarly, all lines interconnecting equipment located on right-hand side of pipetrack are placed to the right of pipetrack. Lines interconnecting equipment located on either side of pipetrack are placed near the center of pipetrack.
10.5 Line Spacing
Use Company job specification no. C100 “recommended pipetrack spacing”
10.6 Road Crossings
The standard method is to provide culverts under access roads. Elevating piping on a cross-over rack is expensive and introduces unnecessary pockets in the lines thus routed. When determining width and height of culvert, care must be taken to allow sufficient room round the pipework for maintenance, insulation and painting. Where only one or two lines cross a road, crossing may be by means of sleeves set under roadway.
10.7 Access Ways
In areas needing frequent access, platforms may be provided across pipetrack.
Where possible, these should be grouped at the edge of an access platform for ease of operation. Drain valves where possible should be brought to outside of pipetrack for ease of operation. The same applies to steam trap assemblies.
10.9 Expansion Loops
Horizontally elevated expansion loops above pipetrack should be provided where necessary. Group all hot lines requiring expansion loops, hottest and largest line on the outside, on one side of pipetrack. (Generally, the side chosen is that side which has the highest number of take-offs serving equipment on that side).
11. Trenched Piping (Civil Department)
In most plants, trenches are avoided due to problems associated with this type of pipeway:
- High initial cost
- Fire hazard
Where trenchers are used to route lines such as:
- Pump out lines
- Chemical sewers
- Chemical drains
Trenchers must be enough to allow sufficient clearance between trench wall and piping. 150 mm between outside of pipe and inside of wall is the minimum acceptable clearance. This will allow for installation of piping, painting and future maintenance. See below figures. Total width of trench required may be determined by using method detailed above. Piping Department will advise Civil Department of requirements.
11.1 Line Spacing
Use Company job specification C100. “recommended piperack spacing”.
Line location in a trench carrying a number of lines should be carefully chosen for maximum piping economy consistent with stress requirements, if any.
Open trenches require drains to stop accumulation of surface water. Trench bottom should be sloped towards drain points. In this case, pipe supporting is by means of angle steel or I beams set into the walls, allowing bottom for free drainage to nearest drain point.
This method allows drainage of a trench by a minimum of drain points between each pipe support as would be the case of solid concrete pipe supports built up from the trench. Before proceeding on trench drainage check with coordination procedure and Civil Department for water table level.
11.2 Safety Precautions
Most trenches have either a cover of concrete slabs or a grating.
Where flammable liquids are carried in trenched lines, a fire break is provided at suitable intervals along a trench and at each intersection. This generally consists of two concrete walls 1 M – 1.25 M apart, with the space in between filled with sand. Where highly flammable gasses are carried, the whole trench, after installation of piping, is back filled with sand. Piping will advise Civil Department of requirements.
12. Underground Piping (by Civil Department)
Keep buried piping to a minimum. Generally only sewer drain lines and fire mains are located below ground. In some cases due to Client or climate requirements, cooling water lines are also buried below the frost line.
With future maintenance in mind, buried lines should be located well clear of foundations, and if running side by side, well spaced out. A minimum of 300 mm clearance is necessary between foundations and lines and between the lines themselves.
Above ground safe drain-tails will enter below ground drain line via a tundish (concentric reducer normally) or if a sealed system and cooling water lines by a flanged stub raised above ground.
Flanged connections should be a minimum of 300 mm above prevalent grade level. It is advantageous to set a common level for all these take offs at the outset of the job. When locating tie-in connections to underground systems, especially from elevated drain points, and adjacent to equipment plinths, ensure adequate clearance.
All buried steel pipes should have applied a corrosion resistant coating and wrapping.
Deep valve boxes for buried lines should be designed with ample room inside the box for a maintenance man to bend over and use wrenches for tightening flanges of re-packing valves. Consideration should be given to the use of concrete pipe in lieu of square boxes.
The criteria for a good underground piping design should be ease of maintenance. Piping should be so spaced as to allow easy digging out and replacement of faulty sections; for this reason, never run underground piping under or through foundations.
Figures – Table
TYPICAL PIPE RANK BENTS
|TYPE||TOTAL AVAILABLE WIDTH W IN mm||PIPERACK||CANTILEVER||NUMBER|
|No.||WITHOUT CANTILEVER||WITH CANTILEVER||WIDTH A||WIDTH B||OF ELEV.|
|2||6000 TO 7300||9150 TO 10400||6000 TO 7300||1500||1|
|3||8500 TO 9750||11600 TO 12800||8500 TO 9750||1500||1|
|4||11900 TO 14300||13700 TO 16150||6100 TO 7300||900 OR 1200||2|
|5||16800 TO 19200||18600 TO 21000||8500 TO 9750||900 OR 1200||2|
|6||8500 TO 10400||11000 TO 12800||6100 TO 7300||900 OR 1500||1.5|
|7||12200 TO 13400||14650 TO 15850||8500 TO 9750||900 OR 1500||1.5|
TYPICAL PIPE RANK INTERSECTION
SINGLE TIER RACK TURNING THROUGH 90°
CROSS-SECTION OF SINGLE LEVEL PIPE RACK
PIPE RACK LAYOUTS
PIPE RACK LAYOUTS
SPACING PIPE TRACK SLEEPERS
Table of Contents
- Hazardous and Toxic Areas
- Economic Considerations
- Aesthetic Considerations
- Site Considerations
- External Influences
- Columns and Drums (Vertical/Horizontal)
- Furnaces and Fired Equipment
- Access to Valves and Instruments
- Relief Valve Systems
- Maintenance and Equipment Handling
Equipment should be laid out in a sequence to suit the process flow. Fluid flow requirements, for example gravity flow systems, pump suction heads and thermosyphon system, often dictate relative elevations and provoke the need for structures. Limitations of pressure or temperature drop in transfer lines decide proximity of furnaces, reactors, etc.
2. Hazardous and Toxic Areas
Equipment items considered a possible source of hazard should preferably be grouped and located separately, if possible and economic.
Furnaces, flare stacks, or other direct fired equipment containing an open flame; rotating or mechanical equipment handling flammable or volatile liquids which could easily leak or spill.
Equipment handling acids or other toxic materials which could cause damage or danger by spillage, should be grouped and contained within a bunded area.
2.1 Locate Control Rooms
15 meters or more from equipment which in operation or during maintenance can create a hazard. (If not practicable, pressurize). Ensure maximum cable run to any instrument is not more than 90 meters.
2.2 Locate Buildings
Example offices, first-aid rooms, cafeterias, garages, fire station, warehouses, gas holders and work-shops a minimum of 30 meters from any hazard.
Unpressurised substation and switchrooms a minimum of 15 meters from any hazard.
Definition of dangerous areas and their safety requirements shall be in accordance with the Institute of Petroleum Safety Codes, or where this is not recognized, to the applicable National Code(s).
Local bye-laws and Fire Office whose requirements may be more stringent or specific than the above codes shall take precedence.
3. Economic Considerations
Apart from process restrictions, position equipment for maximum economy of pipe-work and supporting steel. As compact a layout as possible with all equipment at grade is the first objective, consistent with standard clearances, construction and safety requirements.
Minimize runs of alloy pipework and large bore pipe without the introduction of expensive expansion devices.
Optimize use of supporting structures in concrete or steel by duplicating their application to more than one item of equipment and ensuring that accessways, platforms, etc., have more than one function. Space saving can be achieved by locating equipment over the piperack. Pumps should in general be located with their motors underneath the main piperack.
4. Aesthetic Considerations
Attention should be paid to the general appearance of the plant. An attractively laid out plant with equipment in straight lines is usually economical. Preference should be given to use of a single central pipeway with a minimum number of side branches, with equipment laid out in rows on either side. Buildings, structures and groups of equipment should form neat, symmetrical, balanced layout, consistent with keeping pipe runs to a minimum.
Towers and large vertical vessels will be arranged in rows with a common center line if of similar size, but line up with a common face if diameters vary greatly. If adjacent to a structure, common face will be on the structure side.
Center lines of exchanger channel nozzles and center lines of pump discharge nozzles should be lined up. Piping around pumps, exchangers and similar ground-level equipment should be run at set elevations, one for north-south and another for east-west elevations wherever possible. (Similar for rack pipe-work). These elevations being to bottom of pipe or underside of shoe for insulated lines. This should also help to achieve a common elevation for off takes from pipeways.
If possible, duplicated streams should be made identical. Handed arrangements should be avoided. Follow this principle for this similar equipment sequences within the process stream, for example, fractionator tower with overhead condensers, reflux drum pumps and reboiler, etc., is a system which could be repeated almost identically for different towers having a different process duty. Advantages are design and construction economy, improved maintenance and operating efficiency.
Overall plant arrangement must be reviewed for constructions, operation, safety and maintenance. Consider large items of equipment or towers for which special lifting gear will be required. Provide adequate access to lift these into place. Large equipment positioned close to boundary limits may require erection from outside.
Check to ascertain whether sufficient space will be available at the construction phase.
Operation and maintenance should be reviewed by the eventual operating company. Give consideration to maintenance access to air fins, etc., above pipe tracks.
Consider location of equipment requiring frequent attendance by operating personnel and relative position of control room to obtain shortest and most direct routes for operators when on routine operation.
Provide: Sufficient clear area between critical or high temperature items of equipment. Clear routes for operators with two or more escape ladders or exits at extremities. Clear routes for access by fire-fighting equipment.
Do not Allow: Areas classified as hazardous to overlap the plot limits or extend over railways where open firebox engines are likely to be employed.
7. Site Considerations
Ascertain soil loading considerations and site contours before fixing final layout. Considerable variations occur in allowable soil loads throughout site areas. It may be advantageous to locate heavy equipment in the best soil loading area. Use existing contours, so that the quantity of earth movement due to cut and fill may be substantially reduced by intelligent positioning of the equipment.
8. External Influences
Stacks should preferentially be located so that prevailing winds do not blow smoke over the plant. Try not to locate the plant where it will receive dust, smoke, spray or effluent from a neighboring plant.
Avoid using locations polluted by continuous drift of dust, smoke, etc.
If the plant is to be located in an existing refinery or factory site, line up with existing roads, columns, stacks.
Location of external railways, pipeways, cableways, sewers and drains, etc., may also influence the final orientation of the plant.
When railway facilities are required, avoid boxing in the plant by branch lines.
Hazardous areas from other existing plants or equipment may extend over the plant limit. This could effectively reduce plot size and thus influence the plant layout philosophy.
(See Table A) Clearances between adjacent plants should at least equal those for primary access roads. The space between edge of any road and nearest equipment must not be less than 1.5 meters.
Adequate road access with properly formed roads must be provided for known maintenance purposes: e.g., compressor house, large machinery areas, reactors or converters where catalyst removal and replacement must be effected.
Equipment requiring infrequent maintenance such as exchanger tube bundles, tower internals, etc., need adequate level clear space for access/removal purposes. The ground need not be specifically built up to take loads other than a surfacing of granite chips or similar, as duckboards, gratings, or other temporary material can be laid at the time when the plant is under maintenance.
Within the process area minimal concrete paving should be supplied for walkways interconnecting major items of equipment, platforms, stairways and buildings.
Paving should be supplied around pumps or other machinery located in the open, underneath furnaces, and any other areas where spillage is likely to occur during normal operation.
Areas containing alkalis acids, or other chemicals or toxic materials should be paved and bunded to prevent spillage spreading. Other areas of the plant are to be graded and surfaced with granite chips or similar material.
(See Table A) All elevations refer to a nominal 100 meters. The point 100 elevation is taken as the high point of paving in the paved areas. This should be common throughout the plant. Equipment elevations referring to grade elevations of 100 meters are as shown in table A.
Insulation may be applied to vessel supports or stanchions of structures for fire protection purposes, thus decreasing available free space for access, siting of pipework, instruments or electrical equipment.
In particular, note thickness of insulation of very high temperature or low temperature piping, which may considerably increase effective o/d of pipe to be routed. For low temperature insulation, additional clearance must be provided around control valves, instrumentation, etc. Consider additional weight of insulation and reduced centers of supports necessary to support heavily insulated pipe.
13. Columns and Drums (Vertical/Horizontal)
Columns are usually self-supporting without external structures. Circular or segmental platforms with ladders are supported from the shell. Maximum allowable straight run of ladder before a break platform should not exceed 9 meters.
Factors influencing column elevation are provision of gravity flow system and installation of therm-syphon reboilers. Depending on plant arrangement columns may have to be elevated to a height in excess of the normal requirements to allow for headroom clearance from low level piping off-takes.
Skirt height of all columns or vessels providing suction to pumps, particularly if handling hot or boiling liquids, should be adequate for pump NPSH requirements.
Provide platforms on columns for all valves 3” and above, instrument controllers and transmitters, relief valves, manholes and blinds or spades. Otherwise, access to small valves, indicating instruments, etc., is acceptable by ladder.
Platforms for access to level gauges and controllers should not be provided if underside of supporting steelwork is less than normal headroom clearance from grade. Adjacent columns should be checked, so that platforms do not overlap. For layout, 2.0 to 2.5 meters between shells, depending upon insulation, should suffice. Allow 900 meters minimum clearance between column foundation and adjacent plinth. Provide clearance for removal of internals and attachments, and for davits at top of column if relevant.
Center line of manholes will be 900 mm above any platform.
Horizontal vessels should be located at grade, with longitudinal axis at right angles to the pipeway if possible. Consider saving plot space by changing vessels from the horizontal and by combining vessels together with an internal head. (Subject to project approval). Size and number of access platforms on horizontal vessels shall be kept to a minimum and are not to be provided on horizontal vessels or drum when the top of the vessel is 2.5 meters or less from grade.
Channel end of vessels provided with internal tubular heaters will face towards open space. Withdrawal area must to be indicated on studies, GA’s and Plot Plants. Internal agitators or mixers are to be provided with adequate clearance for removal. Removal area must be indicated on Studies, GA’s and Plot Plants.
Tubular exchangers usually have standard length tubes of 2.5, 4, 5, and 6 meters.
Whenever possible locate exchangers at grade to facilitate maintenance and tube withdrawal. Two or more shells forming one unit will be stacked, or otherwise arranged as indicated on the exchanger specification sheet.
Exchangers on dissimilar service may be stacked but never more than three high, except for fin tube type units. Horizontal clearance of at least 900 mm will be left between exchangers or exchangers and piping. Where space is limited, clearance may be reduced between alternate exchangers, providing sufficient space is left for maintenance and inspection access.
Tube bundle removal distance will be minimum tube length plus 900 mm. Minimum removal distance plus 600 mm will be left behind the rear shell cover of floating head exchangers. Where rear shell cover is provided with a davit, allow clearance for full swing of the head. Set overhead vapor exchangers or condensers at such elevation that exchanger is self draining.
Arrange outlets to a liquid hold pot or trap, so that underside of exchanger tubes is above the liquid level in the trap. Arrange exchangers so that fixed end is at the channel end. Vertical exchangers should be set to allow lifting or lowering of tube bundle. Consult Vessel Section as to feasibility of supporting vertical exchangers from associated towers.
Space for tube or bundle withdrawal should be left free, exchanger channels preferably pointing towards access area or road. If exchanger is situated well within the plot, leave a free area and approach for mobile lifting equipment. Preferably air fin exchangers should be located in a separate row outside the main equipment row, remote from the central pipeway. Consider location of air fin exchangers over the central pipeway if plot space if very limited.
15. Furnaces and Fired Equipment
Locate at least 15 meters away from other equipment which could be a source of spillage or leakage of gas.
No pits or trenches permitted to extend under furnaces or any fired equipment and if possible to be avoided in furnace areas.
Ensure ample room at firing front for operation and removal of the burners and for burner control panel if required.
Bottom floor fired furnaces require adequate headroom underneath the furnace. Wall fired furnaces require an adequate platform width with escape routes at each end of the furnace.
Apart from adequate platforming and access to the firing front, other structural attachments and platforming around furnaces should be kept to a minimum. Peep-holes should only be provided where absolutely necessary. Access by means of step ladder is sufficient.
Arrange heaters on common center line wherever possible. Provide unobstructed space for withdrawal. Operation and maintenance platforms should be wide enough to permit a 1.0 meter clear walkway. Escape ladders should be provided on large heaters. Vertical heaters are usually supplied with stub supporting feet, ensure drawings show adequate supports elevated to required height. Headroom elevation from floor level to underside of heater should be 2.3 meters, to provide good firing control operation.
Locate pumps close to the equipment from which they take suction possibly under structures or with motor ends under a piperack allowing an access aisle for mobile handling equipment. Suction lines are generally larger than discharge lines, to avoid problems arising from low NPSH.
End suction, top discharge is preferable for pumps taking suction directly from tanks or vessels located at grade. Pumps should be arranged in rows with center line of discharges on a common line. Clearances between pumps or pumps and piping shall be a minimum of 900 mm.
Locate reciprocating compressors, anchors and restrains for pipes in the compressor system on foundations independent of any building, structure or pipe trestle.
Spacing varies with type and duty, pay particular attention to: Withdrawal of engine and compressor pistons, cam shaft, crank shaft and lube oil cooler bundle; cylinder valve maintenance clearance with least possible obstruction from piping supports.
Compressors are generally provided with a degree of shelter, i.e., a sheets building. Keep the sides up to 8 feet above grade, open and vent the ridge to allow for escape of flammable gas which might leak from the machines. Certain types of compressors, owing to the height of the mass foundation above grade level, require a mezzanine floor of the grid construction to avoid trapping any gas, for operation and maintenance.
All piping within a process area should usually be run above grade. Trenched piping to be avoided. Piperacks and supports to be of the simplest form.
Piperacks may contain two layers of pipework. Avoid triple layer of pipeways except for very short runs. Run piping external to the process area at grade on sleepers (300 mm high). (Piping at grade is cheaper but liable to interfere with access).
Locate large bore piping as close to stanchions as possible. Lines requiring a constant fall (relief headers) can be run on cantilevers from piperack stanchions or on vertical extensions to pipe track stanchions.
Run hot line requiring expansion loops on the outside edge of pipeway to permit loops to have greatest width over the pipeway and facilitate nesting. Take-off elevations from pipeways should be at a constant elevation consistent with the range of pipe sizes involved.
Change elevation whenever banks of pipes, either to grade or on piperacks change direction. Elevations to the underside of piperacks will be minimum for operation and mobile maintenance equipment and consistent with clearances.
Open pipe trenches may be used between plants where there is no risk of flammable vapors collecting. It is sometimes convenient to run open trenches alongside roadways. (Soil from the trench can be used to build up the road). Where a pipeway or road changes direction, the pipe is run beneath the road. Occasionally it is permissible to run pipes in trenches to overcome a difficult piping problem. Such trenches should be concreted, drained and covered. Although trenched piping is to be avoided due to the expense and hazards associated with open trenches, underground buried piping is acceptable provided pipe is adequately protected and below the frostline.
Sizing and arrangement of underground piping should be fixed early to ensure that installation is simultaneous with foundation work. (Many drains, sewers and cableways, which do not require attention, are run underground below the frost-line). Leave space for drawboxes on cableways, anchors on underground cooling water pipes and manholes on sewers. Fire mains should be located between the perimeter road and the plant.
19. Access to Valves and Instruments
(See Table A)
All operating valves 3” and larger are to be accessible either from grade or suitable platform with maximum 2.0 meters above working level to center of hand-wheel. Small operating valves can be reached from a ladder. Valves installed for maintenance and shutdown purposes (other than operating) can be reached by portable ladder. Otherwise extension spindles or suitable remote operating gear should be provided, but not on valves 1 1/2” and below. The minimum access to be provided is as shown on Table A.
20. Relief Valve Systems
Closed relief valve systems should be arranged to be self-draining and should not contain pockets where liquids may condense and collect to provide any back pressure.
21. Maintenance and Equipment Handling
Handling facilities are limited to the handling of working parts of equipment which require frequent or routine service and which are inaccessible to mobile handling facilities assumed to be available at the plant. These facilities are not designed to handle heavy parts such as bedplates of rotating machines, rotating equipment, compressors’ bodies, machinery frames, etc. The handling facilities provided are limited as shown on table A -
The design and installation of trolley beams, overhead travelling cranes and hoist trestles is based on lifting the parts to be handled and transporting or lowering them to specified maintenance areas or to grade. From these points they are expected to be removed by skids or hand trucks to other areas more suitable for maintenance.
|Clear Headroom||Clear Width||Other Clearance|
|Primary Access Roads (carrying major equipment)||6M||6M||10.5M inside corner radius|
|Secondary||5.1M||4.8M||4.5M inside corner radius|
|Minor Access Roads||5.1M||3.6M||-|
|Platform, walkways, passageways, working areas, stairways||2.1M||1M working platforms||-|
|Clearance from face of manhole||2.1M||1M||Manhole centre Approx. 1M above platform|
|Railways||To suit local codes||-||-|
|Open-Air Paved Area High Point of Paving||100.000M|
|Underside of baseplates for structural steel||100.150M|
|Stair and ladders pads||100.075M|
|Underside of baseplates vessel and column plinths||100.300M|
|Top of pump plinths||100.230M|
|ITEM||MINIMUM ACCESS FROM||LOCATE OVER|
|SIZE||FIXED LADDERS||EDGE OF PLATFORM||PLATFORM OR GRADE|
|OPERATIONAL VALVES||2” and under||X||-||-|
|OPERATIONAL VALVES||over 2”||-||X||-|
|MOTOR OPERATED VALVES||all||-||X||-|
|R.V.’s (Process)||2” and over||-||-||X|
|BLOCK VALVES||Accessible by portable ladder.|
|BATTERY LIMIT VALVES ETC.||ALL||Edge of platform access where Client’s Spec. requests. Otherwise no access.|
|PROCESS BLINDS AND SPADES||ALL||-||-||X|
|NOZZLES||ALL||No access Provided.|
|LINE DRAINS AND VENTS||No access Provided.|
|EQUIPMENT||PART HANDLED||HANDLING FACILITIES|
|Reactors, Vessels and Columns.||Manhole Covers||Davits or hinges for swinging open.|
|Internal requiring regular removal or servicing.||Trolley beams or davits for lowering from holes to grade.|
|Fixed bed reactors, catalyst change, etc.||These will be provided as specially specified to enable catalyst to be offloaded and loaded.|
|Floating Head Exchangers.||Tube Bundles.||All such exchangers are provided with jackbolts to break joints. It is assumed bundles will be handled by mobile equipment.|
|Exchanger Heads, Channel Cover, Bonnets.||No special provision.|
|Vertical Exchangers.||Removable Tube Bundles.||Overhead trolley beam or davit.|
|Centrifugal Compressors.||Rotating parts.||Overhead trolley beams or cranes.|
|Piping.||Relief Valves, 2” nominal bore and larger.||Hitching point or davit for lowering to grade.|
|Blanks, blank flanges and swing elbow weighing more than 300lbs (125 kg).||Overhead hitching point or davit only when subject to frequent removal for maintenance.|
Listing of Instrumentation Which May Assist Initial Layout
Likely Devices and Probable Number Fitted to Various Types of Equipment. Devices and Design Points Affected.
|EQUIPMENT||DEVICES AND PROBABLE NUMBER OF ITEMS FITTED|
|DISTILLATION TOWER||PSV (1) (Pressure Safety Valve)
PIC (1) (Pressure Indicating Controller)
FRC (3) (Flow Recording Controller)
TR (1) (Multipoint- 6 channel) (Temperature Recorder) TI (6) (Temperature Indicator)
PI (6) (Pressure Indicator)
Analyser (1) (Single Stream)
LG (2) (Level Gauge)
LI (1) (Level Indicator)
LIC (1) (Level Indicating Controller)
|REFLUX DRUM SURGE DRUM BUFFER STORAGE FEED TANK PRODUCT TANK||LG (3) (Level Gauge)
LIT (1) (Level Indicating Transmitter)
PI (1) (Pressure Indicator)
TI (1) (Temperature Indicator)
PSV (1) (Pressure Safety Valve)
PIC (1) (Pressure Indicating Controller)
|REACTOR||PI (6) (Pressure Indicator)
TI (6) (Temperature Indicator)
PSV (1) (Pressure Safety Valve)
TR (1) (Multipoint- 50 Channels) (Temperature Recorder)
FIC (2) (Flow Indicating Controller)
LIC (1) (Level Indicating Controller)
PIC (1) (Pressure Indicating Controller)
TIC (1) (Temperature Indicating Controller)
|EQUIPMENT||DEVICES AND PROBABLE NUMBER OF ITEMS FITTED|
|COMPRESSOR (Axial flow)||PI (4) (Pressure Indicator)
DPC (1) (Differential Pressure Controller)
PIC (1) (Pressure Indicating Controller)
FR (1) (Flow Recorder)
TI (1) (Multipoint- 12 channel)(Temperature Indicator) Vibration (2)
NRV (Damped to prevent reverse flow)
Programmer and Logic System (1)
Shutdown System (1)
|COMPRESSOR DRIVER (Steam turbine)||PI (4) (Pressure Indicator)
FRC (1) (Flow Recording Controller)
TI (4) (Temperature Indicator)
Shutdown Valve (1)
|EXCHANGER||TRC (1) (Temperature Recording Controller)
TI (6) (Temperature Indicator)
PI (2) (Pressure Indicator)
LG (1) (Level Gauge)
PSV (Pressure Safety Valve)
|FURNACES||FRC (4) (Flow Recording Controller)
TRC (Temperature Recording Controller)
PIC (Pressure Indicating Controller)
Flame Detector (2)
PI (12) (Pressure Indicator)
|EQUIPMENT||DEVICES AND PROBABLE NUMBER OF ITEMS FITTED|
|FURNACES (cont’d)||TI (6) (Temperature Indicator)
Multi-channel Temperature (1)
O2 Analyser (1) (Only where BFW or steam is circulating)
pH Analyser (1)
LG (3) (Level Gauge)
LIC (1) (Level Indicating Controller)
PSV (3) (Pressure Safety Valve)
PCV (3) (Pressure Control Valve)
In-line instrument elements:- Flow Elements (Orifice, Plates, Venturi, Turbine, P/D, etc.). Control Valves (Globe, Butterfly, Ball, etc.). Relief Valves. Thermowells. LIST 2)
|DEVICE||TYPE||DESIGN POINTS AFFECTED|
|Fe 1||Pipe Section with sensing element||Flange rating/size/overall length/orientation|
|Fe 2||Pitot Tube||Location/straight length connection size & type|
|Fe 3||Orifice/Nozzle/Venturi||Location/straight lengths/orientation Flange size and rating. Position, size type of instr. tappings|
|Fe 4||Elbow||Size/end connections/orientation straight lengths|
|Fe 5||Target Meter Transmitter||Orientation/straight lengths/Flange rating/ connections/ insertion face to face|
|Fe 6||Vortex Meter||Orientation/straight lengths/Flange rating/ face to face/insertion|
|Fe 7||Hot Wire||Consult Instrument Department|
|Fe 8||Variable Area Meter||Vertical only/Flow upwards only. Orientation of connections, sizes and type.|
|Fe 9||Magnetic Flowmeter||Overall length/size/connections/vertical or horizontal/no straight lengths.|
|Fe 10||Turbine Meter||Straight length/with or without pipe section/ usually horizontal end connection and size. (Common to use upstream filter and sometimes degassing).|
|Fe 11||Positive Displacement||Orientation one way only/weight/no straight lengths. Connecting as per vendor literature.|
|Fe 12||Sonic Flowmeter||Consult Instrument Department|
|Fe 13||Weight Rate||Consult Instrument Department|
|Fe 14||Radio Active||Consult Instrument Department|
|Fe 15||Photo Electric||Consult Instrument Department|
|Fe 16||Channels and Flumes||Mostly Civil Engineering.|
|Fe 17||Vane Type||Spool piece = face to face end connections.|
|DEVICE||TYPE||DESIGN POINTS AFFECTED|
|TE 2||Resistance Bulb||Location/Increase in pipe dia/elbows, connection size and type.|
|TE 3||Filled System|
|TE 5||Radiation||Location of window/heat protection.|
|Be||Photo Electrical/Colour||Location of instrument and window.|
|An||Diverse Methods includ- ing SG and density||Usually with by-pass line to drain on back to process – only occasionally in line – some- times co-axial spool piece. Face to face/Flanges.|
|An||Capacitance||Similar to temperature Te 1.|
|Probe||Conductivity||Sometimes co-axial in spool piece.|
|PROXIMITY||Fero magnetic)||Non intrusive|
|SWITCH||Magnetic)||Location and mounting|
b) Instrusive, type Te 1.
|Differential Pressure||Bourdon Tubes Capsules Strain Gauge||Small tapping/location/connections/ size and type|
|DEVICE||TYPE||DESIGN POINTS AFFECTED|
|LG||ALL TYPES||Vertical only – nozzle spacing/connections|
|LG||ALL TYPES||Vertical only – nozzle spacing critical/connections|
|MEASUREMENT||Magnetic||Consult Instrument Department.|
|Strobe Tachiometer||Consult Instrument Department. Consult Instrument Department.|
|PV, FV, TV, etc PVC||Operation-electrical -hydraulic -pneumatic -self operated||Nominal body size is determined by flow criteria. Face to face/connection sizes – flange rating often 300lbs minimum as a standard. Axis of movement of topworks must be vertical-all other orientation prohibited. Face to face dimensions do not always conform to BS.|
|PSV||Spring opposed pressure||Free or closed venting. Multiple valve relief. Gauge valves with single operation of changeover – single isolation valves prohibited – minimum nozzle size laid down in the codes. Some inlet/outlet flange combinations are excluded in standard manufacture depending on application.|
GENERAL NOTE: Instrusive elements and/or spool type installation may call for flow line size due to change due to forces on wetted parts, erosion, noise, deposition of solids in cavities or viscosity.